why is the vector group analysis done in transformer tests
Answers were Sorted based on User's Feedback
Answer / j
To determine phase displacement
|Is This Answer Correct ?||231 Yes||13 No|
Answer / pratik
It is to be carried out to check whether the transformer
under test is suitable for parallel operation with another
transfomer having same vector group and voltage ratio but
difference in KVA rating.
|Is This Answer Correct ?||192 Yes||35 No|
Answer / sachin
Vector group analysis done in transformer test, so that we
can check the phase displacment and polarity of the
|Is This Answer Correct ?||119 Yes||17 No|
Answer / eka
parralling operation of trasformer
|Is This Answer Correct ?||48 Yes||8 No|
Answer / fred jabagat
Vector Group can be used as basis in setting the phase
compensator factor for numerical transformer differential
relays, i.e. SEL387.
A 3-Ph Transformer is wired internally in different ways to
produce a desired phase position between primary and
IEC standards develop a transformer circuit configuration
and a corresponding vector group code which follows a clock
that represents a 30 degrees shift in every hour.
The CT's of a numerical transformer differential relays are
usually wired with its polarity mark facing away from the
protected winding. Because of the phase shift between the
primary and secondary terminals of the transformer it is
necessary to set a phase compensator factor to the
differential relay so that it will not trip on normal load.
|Is This Answer Correct ?||38 Yes||6 No|
Answer / saju thomas
Mostly using transformer phasing arrangements are
DYn11,DYn7,DYn5.This is related to phase
displacements.vector group test is doin for analaysing
transformer phaseangles as per the phasing arrangements
like DYn11 or DYn7 or ...
|Is This Answer Correct ?||40 Yes||11 No|
Answer / shrinivas
vector group are made to know at what position the secondary
winding of transformer we get star and delta voltages . and
it indicates the type of winding in primary and secondary
which helps in parallel operation of transformer with
different ratings having same vector group .
|Is This Answer Correct ?||41 Yes||13 No|
Answer / joe callaghan
Transformer vector relationship is tested by shorting the
primary A phase to secondary A phase, then applyying a
three phase voltage to the primary side of the transformer.
Voltage measurements are then taken as follows:
These values will then allow you to draw the vector diagram
of the transformer.
|Is This Answer Correct ?||32 Yes||9 No|
Answer / dinesh kumar
1,Vector group is done on transformer High voltage winding
with respect low voltage winding.
2,To find the phase angle/difference between different
connections in high voltage windings.
3,In three phase winding transformer there are 36 vector
|Is This Answer Correct ?||54 Yes||39 No|
Answer / dhaval
to determine the primary and secondary winding of the
tranformer that how the winding is connected
|Is This Answer Correct ?||20 Yes||6 No|
What is meant by pilot exciter and its working?
why we are not earthing ht cable at both the ends(sending & receiving end)?
what is negative,positive abd zero sequence current explain clearly
Which do you think is the most significant cause of energy loss in a factory?
What is a charge.?
Sir I hv to fix 20 ton ac how much electrical power need apply?
we know that dc motors are more superior then three phase induction motors in torque generation though they are not much used in industries why?
in Contactor opearation Why there is a difference in the values of the operate and release voltage in case AC supply
Why we are using air gap magnetic condutors
Maximum efficiency occurs in electrical machines is at i)Full load,ii)50% of full load,iii)Near full load,iv)None of these
why transformer neutral and CT Secondary neutral is connected to earth?
What will happen if " not connecting the neutral point to ground of diesel generator output (380 V)", also if someone touched one phase without isolation from ground during the A/M condition what will happen to him?