Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

How to take Vector group test of Transformer?

Answers were Sorted based on User's Feedback

How to take Vector group test of Transformer?..

Answer / dinesh kumar

Assumed the transformer vector group is DYn11;
1.1U1V1W-which is primary -Delta Connection
2.2U2V2W- Which is secondary-Star connection
3.join 1U& 2U terminals
4.Supply 1U-1V-1W 440v Measured
a.1U-1V
b.1V-1w
c.1W-1U
d.1W-2W
e.1V-2W
f.1V-2V
g.1W-2V
h.1U-2N
i.1V-2N
TO CHECK
1.1V-2W=1V-2V
2.1W-2V>1W-2W
3.1U-1V=1V-2N+1U-2N
From above check(1,2,3) the vector group of transformer is
verified

 Is This Answer Correct ? 225 Yes 28 No

How to take Vector group test of Transformer?..

Assumed the transformer vector group is DYn11;
1.1U1V1W-which is primary -Delta Connection
2.2U2V2W2N- Which is secondary-Star connection
3.By connecting terminals 1U& 2U
4.Then three phase Supply is given to 1U-1V-1W
5.By measuring the terminal given below
We get
a.1U-1V
b.1V-1w
c.1W-1U
d.1W-2W
e.1V-2W
f.1V-2V
g.1W-2V
h.1U-2N
i.1V-2N
THE BELOW GIVEN CONDITION IS SATISFIED THEN DYn11 IS
CONFIRMED
1.1V-2W=1V-2V
2.1W-2V>1W-2W
3.1U-1V=1V-2N+1U-2N

 Is This Answer Correct ? 121 Yes 26 No

How to take Vector group test of Transformer?..

The above method is correct

 Is This Answer Correct ? 45 Yes 12 No

How to take Vector group test of Transformer?..

wht abt YN d11 transformer...??????

 Is This Answer Correct ? 28 Yes 13 No

How to take Vector group test of Transformer?..

Vector group is punched on the name plate based on the user
requirement by the manufacture. Aim of vector group test is
at site is to check if their is any damage in the windings
during transportation and erection.
3 -phase AC supply is given on HV side. R-Phase HV and r-
phase LV shorted for all vector group of transformer

Then to qualify the test following conditions are to be
satisfied after measurement of voltages.

nR+nY=RY, By>> Bb and Yb=Yy.

 Is This Answer Correct ? 19 Yes 5 No

How to take Vector group test of Transformer?..

can anyone say me hoe to draw vector group and what is the
use of different vector group and its application plz

 Is This Answer Correct ? 18 Yes 8 No

How to take Vector group test of Transformer?..

Procedure given by Mr. dinesh kumar & Mr. E.saravanan is
correct but is there any explanation for this three
conditions.
1.1V-2W=1V-2V
2.1W-2V>1W-2W
3.1U-1V=1V-2N+1U-2N

 Is This Answer Correct ? 13 Yes 3 No

How to take Vector group test of Transformer?..

1U-1V=[1U-2N]-[1V-2N]

 Is This Answer Correct ? 11 Yes 4 No

How to take Vector group test of Transformer?..

1.1U1V1W-which is primary -Delta Connection
2.2U2V2W- Which is secondary-Star connection
3.join 1U& 2U terminals
4.Supply 1U-1V-1W 440v Measured
a.1U-1V
b.1V-1w
c.1W-1U
d.1W-2W
e.1V-2W
f.1V-2V
g.1W-2V
h.1U-2N
i.1V-2N
TO CHECK
1.1V-2W=1V-2V
2.1W-2V>1W-2W
3.1U-1V=1V-2N+1U-2N
From above check(1,2) the vector group of transformer is
verified

 Is This Answer Correct ? 9 Yes 3 No

How to take Vector group test of Transformer?..

Answer / vinay kumar

can anybody tell hw u r writing this is the vector group
calculation for this one.....
what happens if the voltages r not satisfied for the
specified vector group and if so what to do.......

 Is This Answer Correct ? 7 Yes 3 No

More Electrical Engineering Interview Questions

State kirchoff current law?

What is Earth Fault and Over current Fault.

why nutral and earthing wire connect with each other in main panel board.?

what is mean by ideal infinite bus? why it is required to consider in fault short circuit calculations?

what is the difference between gsm and cdma??

IF ANY MATERIAL AVAILABLE IN MARKET FOR MOTOR PROTECTION INSTEAD OF OLR & CONTACTOR ?

what is the formula for calculating of dielectric strength of transformer oil.

Hi Friends pls give information regarding BARC written test. am attending by 20-5-2008. mail me to kkumarei@gmail.com or message to 9962122264

WHY HVDC?

we all know that in capacitor there will be no ay physical connection between the two electrodes of the capacitor ,and the charge is stored between these electrodes during charging , so with out any physical connection how these charge is transferred from one plate to the another plate during the discharge?????

by using pump duty, how we will can calculate the motor duty(KW)? is there any standard or formula.

what is meant by reactive power ,active power & real power ? thank you

Categories
• Civil Engineering (5081)
• Mechanical Engineering (4448)
• Electrical Engineering (16620)
• Electronics Communications (3915)
• Chemical Engineering (1093)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2994)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (171)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1379)