What is the rating of your capacitor bank at your company.
Answers were Sorted based on User's Feedback
Answer / sharma jiten
The most common method for improving power factor is to add
capacitors banks to the system. Capacitors are attractive
because they're economical and easy to maintain. Not only
that, they have no moving parts, unlike some other devices
used for the same purpose.
When you add a capacitor bank to your system, the capacitor
supplies the reactive power needed by the load. If you size
and select the capacitor bank to compensate to a unity
power factor, it can supply all the reactive power needed
by the load, and no reactive power is demanded from the
utility. If you design the capacitor bank to improve the
power factor to a quantity less than 1.0, the reactive
power supplied by the bank will be its rated kVARs (or
MVARs), while the rest of the reactive power needed by the
load will be supplied by the utility.
|Is This Answer Correct ?||119 Yes||11 No|
Answer / vishwas
|Is This Answer Correct ?||33 Yes||7 No|
Answer / vara prasad
guys this question does't mean that to specify your
company's capacitor bank capacity .... please answer in
general how to calculate your required capacity of
capacitors at your company depending on load
|Is This Answer Correct ?||27 Yes||3 No|
Answer / rajendran.m
17 no's 25 kvar
|Is This Answer Correct ?||26 Yes||9 No|
Answer / chandru
The addition of capacitance depend upon your power factor.suppose u may get more than 0.97 or unity Pf,u no need to add capacitor.becoz it may act like load
|Is This Answer Correct ?||8 Yes||1 No|
Answer / sudheer
50 kvra eacth amount
|Is This Answer Correct ?||13 Yes||7 No|
Power factor is only present in the ac power supply systems. In dc there is no usage of power factor terms. Ac supply is having frequency and potential is alternating with respective to time as such the load on the ac power source is of mix like capacitance, resistance and inductance
Capacitance is offered by ug cables and heater and filament lamps offer the resistive loads and hid and fluorescent lamps offers inductance value
Inductive reactance (xl) and capacitive reactance (xc) is counter each other and resultant effect will reflect in ac system in addition to normal resistance. This cumulative resistive effect is called as impedence.
Now power factor is equel to pf = r/z.
Now if we draw a power circle the you know the differnce of kw and kva is made by kvar that is reactive power if we reduce this reactive power then the kva demand and kw i mean apparent power and actual power will became more or less equal. Now power factor that is quality power.
So we can improve the power systems by adding counter reactive power by adding capacitors in kvar ratings.
Apfc panels are best suitable for proper monitoring as static correction will not perform well in massive load centres as failure and degradation of capacitor is hard to find out and rectify.
|Is This Answer Correct ?||6 Yes||0 No|
Answer / natrayan
I Need to know the how much capacitor bank that i have to put for these Load KW or HP or KVA
For Example: 15HP we can use 2kVAR of capacitor
|Is This Answer Correct ?||8 Yes||4 No|
Answer / parag
|Is This Answer Correct ?||8 Yes||6 No|
Answer / prashanth kumar
6300kvar & 2100kvar 11kv
|Is This Answer Correct ?||5 Yes||3 No|
In single phase capacitor motor, if the motor rotate reverse direction then how much power will be consumed by the motor and why?
Write down the design procedure of commutaj.
sourse is 66 KV / 350 MVA, transfarmer is 1000 KVA 6.6 / 0.415 kv, iF fault is 28.75 MVA on 0.415 KV Bus then calculat the Transfarmer Impidance
Why more than 2.5 MVA distribution transformers (secondary is 440V)are not used in india.
Dear all, kindly give me the details of leectrical design engineer course details/institute in hyderabad /any where in india.
what is the difference between indoor package substation and outdoor
what is 'A' Check & 'B' Check ?
how to find the transformer neutral copper earthing size
why ct is connected at bushing of transformer ??????????
Is there any reason that a vertical motor can not be mounted horizontally ? I happen to have one and would like to use it horizontally to save money by not buying a new horizontal motor.
Wt is the function of reactive power? How it generates & consume though resultant is zero?
what is the phase voltage and line voltage in 2 phase power supply?