Is your generator is automated or manual if so do you know
Answers were Sorted based on User's Feedback
Answer / yuvi
Honestly, this question does not make any sense. However, I
will try to answer to the best of my understanding.
1) I don’t have a generator.
2) Difference between manual and automated generator is
that in a manual start generator, we will have to manually
start it. In an automatic start generator, a circuit senses
that the power has failed and starts the generator
automatically using a small battery powered motor similar
to the ones that start your car. The sensing circuit can be
of a wide variety. It can be a magnetic relay or an
electronic circuit depending on the area of application.
|Is This Answer Correct ?||13 Yes||1 No|
Answer / tapas
in both Auto and Manual cases circuit diagram can be found in the Drawing of Sync panel/AMF panel. Its a selector switch by which user can select either Auto mode or Manual mode.
DG start and stop circuit has two ways to operate which can be found on drawing.
1.Manual Mode: In this mode push button start and push button stop operates DG. i.e. when power fails DG can't be started Automatically. Operator should start the DG manually.
2. Automode: PLC senses absence of Power and commands DG to start.
|Is This Answer Correct ?||11 Yes||0 No|
Answer / ferozuddin
generator wiil be function as a manual and also auto .
manual in case of when there will be no interface with the
auto transfer switch (ATS).when generator is interface with
the ATS it will work auto in case of emergency
|Is This Answer Correct ?||4 Yes||1 No|
Answer / mani0786
mannully start genset start manually & wwhen it come with a amf or ats panel it said auto genset well sir your question is out my mind but so i give it a simple sot
|Is This Answer Correct ?||1 Yes||0 No|
Its very simple
Take an 230v auxillary contactor with 1NO POINT and 1NC POINT
One single phase connect at one side NO POINT and other end connect to contactor A1(NO VOLT COIL).A2NEUTRAL directly connected.
Positive (+) supply24 v connected at NC POINT one side and other end connected at generator starting switch .
When EB powersupply is there the contactor is on.
When EB supply cut through NC POINT the positive supply passing to the switch so the generator is on.
Its very cheap.
|Is This Answer Correct ?||0 Yes||1 No|
Answer / ponvel
|Is This Answer Correct ?||2 Yes||5 No|
How can i check a relay good or not?
what is the difference between online & offline caliberation of KWH meters. Can Digital meters be caliberated
how to diffrentiate between ac & dc motors from a distance
when will cause the negative sequence falut in electrical system?
How to connected to energy meter, pt, ct, ammeter, voltmeter and selector switch.
why neutral and earth should not be connected on 3 phase 440v/50c/s supply at consumer side. where as on 25kv/ac/50c/s railway traction substation neutral and earth will be connected and track at substation. and track will act as neutral and earth. Reasons for this is needed urgently
what is the function of anti-pumping in circuit breaker?
1- What is the Polarization Index number be good for 15KV 3c#500MCM electrical cable? 2- Can I use the IEEE Std 43-2000 to perfom the PI test? Thanks
what is the diference between the 4pole & 6pole DC Motors & what is advantage 6pole over the 4pole ?
In LRS how much water PH value maintain for good operation of motor?
iam preparing for rrb section engineer post in electrical branch.suggest the right textbook for my reference.fromwhere i will get the previous q.papers?
what do you mean by PF correction. A motor is rated at 15 kw,415 volts, 0.7 pf and eff of 0.92. The powerfactor is improved to 0.98 by adding capacitors at the bus. calculate the current drawn by motor under full load condition before and after pf correction