Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

Hello friends i am facing one problem in lighting panel.
Frequently neutral link near to MCCB is burning(firing. What

Answers were Sorted based on User's Feedback

Hello friends i am facing one problem in lighting panel. Frequently neutral link near to MCCB is b..

Mr. sunil.

The possible causes are.

2. loose connection
3. Harmonics in the system

 Is This Answer Correct ? 14 Yes 0 No

Hello friends i am facing one problem in lighting panel. Frequently neutral link near to MCCB is b..

the current rating is greater than the MCCB rating. so go for
higher current rating...

 Is This Answer Correct ? 2 Yes 1 No

Hello friends i am facing one problem in lighting panel. Frequently neutral link near to MCCB is b..

Answer / m v v s n murthy

Generally, we will distribute our 1 phase loads equally in 3
phases to get the balanced load and the circuit becomes star
connected. In star connection, there will be no current in
neutral line if the load is balanced.

In the lighting loads also we have to distribute equally in
3 phases. If not, current will increased in neutral.

In your case you did not devide the lighting load to get
balanced star connection, and also the neutral link in your
MCCB under size to carry unbalanced neutral current. And
also there may be loose connection at neutral link.

 Is This Answer Correct ? 3 Yes 2 No

Hello friends i am facing one problem in lighting panel. Frequently neutral link near to MCCB is b..

Dear friend ,

First measure the current flowing thro MCCB .If it is MCCB
then it must have protective system . Set it as per max
current.measure the neutral current at full load. measure
neutal to earth voltage . most possible reasons are

1] Neutral link is undersized or

2] Loose connections

3] Neutral is not properly earthed .

 Is This Answer Correct ? 1 Yes 1 No

Hello friends i am facing one problem in lighting panel. Frequently neutral link near to MCCB is b..

the mccb is burning because the rating for the current for
which it is selected may not be proper

 Is This Answer Correct ? 0 Yes 1 No

More Electrical Engineering Interview Questions

what does happen if generator frequency fall in running condition & what should require immediately

Compare OH Transmission & UG Transmission?

derive the e.m.f equation of transformer

Dear sir, By which formula u can calculate for a particular kv line there is a range of mw.

what is the significance of positve n negative voltage regulation .on alternator

How to calculate the transmission losses incase of overhead transmission lines?

Application of DC motors is generally restricted to a few load speed applications because of _____.

which protection function should measure RMS value of current&DFT value of current?

PLEASE EXPLANE WHAT IS " MOSFET AC CONVERTER"? WHERE AND HOW IT IS USED?

Find defination of KVA convert in to KW.

what type of insulation is used for over head lines?

Is KCL applicable for close circuit?

Categories
• Civil Engineering (5075)
• Mechanical Engineering (4444)
• Electrical Engineering (16604)
• Electronics Communications (3915)
• Chemical Engineering (1092)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2992)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1377)