Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

I hv a question regarding power factor improvement just
after transformer. I request you to reply me plzz. thank
you sir.
My friend has a small unit of fabrication. in his factory
the main load is a welding machine, lathe machine, grinding
machine. this load is not continuous type. now our
electricity board has installed 16 KVA, 11000/433 V
transformer for our factory. In the energy meter (trivector
meter) at LV side of transformer, i hv seen power factor
value of 0.15 only when only 3 KW load was flowing. Further
electricity board has suggested to install 4 KVAR capacitor
at LV side after energy meter. Now my question is that if
we permanantly install and switch on 4 KVAR capacitor after
energy meter, during some load on transformer and also
without any load on transformer, wht will be the power
factor shown in energy meter?i dont want to get any penalty
by electricity board, so plz suggest me if i can
permanantly install and switch on the 4 kvar capacitor or
not at LV side of transformer just after energy meter?
Thank you again and awaiting for ur positive reply soon.

Answers were Sorted based on User's Feedback

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

the 4kvar capacitor improve the pf but you must keep in
mind that installed the capacitor permanentely only at load
time.switched off the capacitor on unload time since i

 Is This Answer Correct ? 2 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

The purpose of capcitor is to improve pf according to
more current than full load and improve pf.power consuming
by the capacitor is reactive power which will not count by
EM.

required capa.(kvar)=p*(tan(inv cos(pf1))- tan(inv cos(pf2))

p= total power in kw
pf1=actual pf
pf2=required pf

 Is This Answer Correct ? 2 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

You have to calculate and put partially some capacitor
permanentely ON which will neutralized or improve the PF
when Transformer charged with NO load condition and other
capacitor should be connect through contactor so that as
welding machine will on capacitor will on ( interlocking
between both ).If PF increase or reached to Leading side
means it will work as a load and you have to pay extra
PF Calculation Formula

required capa.(kvar)=p*(tan(inv cos(pf1))- tan(inv cos(pf2))

p= total power in kw
pf1=actual pf
pf2=required pf

 Is This Answer Correct ? 2 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

The transformer at no load has a pf depending on relative
A capacitor permanently connected to the LV side should be
of a kVAR value to just correct the inductive kVAR at no-

Separate sets of capacitors should be judiciously applied
to correct the pf on load. The best thing to do is to
switch the pf-improvement capacitors on and off along with
the switching of the individual offending loads (e.g., by
connecting the capacitors of appropriate ratings to the
inherently 'automatic' control of capacitor switching.

 Is This Answer Correct ? 1 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

when the capacitor is switched on at load it will improve
the power factor, but you have to take care that the
capacitor is switched on when there is no load on the
transformer...we have to take care about that...

 Is This Answer Correct ? 2 Yes 2 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

capacitors connected on the lv side at no load will take
charging current...........as a result it will act as a

 Is This Answer Correct ? 0 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

Most of the Elec boards consider only the average pf which
is =Kwh/Kvah for the billing month.Fix individual capacitors

 Is This Answer Correct ? 0 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

Answer / m s venkateswara rao

It is not possible to maintain constant power factor at variable load. A little bit expensive but you have to go for procure auto pf panel, installed and connected immediately after EB meter.In APF panel controller you should set the pf range so that at different loads APF panel will automatically will switch on different rating of capacitors to maintain set pf.

 Is This Answer Correct ? 0 Yes 0 No

I hv a question regarding power factor improvement just after transformer. I request you to reply ..

how capacitors connected in parallel to each phase i.e
R,Y,B giving a resultant of 4 KVAR become a self load at
noload time of transformer and increase the electricity

 Is This Answer Correct ? 0 Yes 1 No

More Electrical Engineering Interview Questions

Explain about retrofitting of machine tool.

How do you connect the capacitors on polyphase circuits?

WHY MOSTLY BATTERY VOLTAGE IS IN MULIPLE OF 2 LIKE 2V,4V,8V,16V,18V....

I NEED RRB CHENNAI (JE ELECTRICAL) QUESTION PAPER FOR LAST 5 YEAR AND I NEED RRB (JE ELECTRICAL) SYLLABUS.PLEASE SEND MY E-MAIL joo28_eee@yahoo.co.in

3-PHASE 15KVA dg IS EQUIVALENT TO 12 KW,hOW?

How much the fault level of 11 k.v.,22 k.v., 33 k.v. (in Maharashtra- M.S.E.D.C.L) for calculation of short circuit current & selection of h.t.cable.

How to calculate phase to phase difference in 33KV Line ,11KV Line etc.

What is the purpose of stand by earth fault protection for transformer ?

why neutral grounding transformer is used for generator and why it is not used for transformers?

what is Thermocouple? Type of its.

explain Xmer

If SFU is Switch Fuse Unit, What is the expansion for FSHF in Electrical Engineering?

Categories
• Civil Engineering (5074)
• Mechanical Engineering (4444)
• Electrical Engineering (16594)
• Electronics Communications (3915)
• Chemical Engineering (1092)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2986)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1377)