I hv a question regarding power factor improvement just
after transformer. I request you to reply me plzz. thank
My friend has a small unit of fabrication. in his factory
the main load is a welding machine, lathe machine, grinding
machine. this load is not continuous type. now our
electricity board has installed 16 KVA, 11000/433 V
transformer for our factory. In the energy meter (trivector
meter) at LV side of transformer, i hv seen power factor
value of 0.15 only when only 3 KW load was flowing. Further
electricity board has suggested to install 4 KVAR capacitor
at LV side after energy meter. Now my question is that if
we permanantly install and switch on 4 KVAR capacitor after
energy meter, during some load on transformer and also
without any load on transformer, wht will be the power
factor shown in energy meter?i dont want to get any penalty
by electricity board, so plz suggest me if i can
permanantly install and switch on the 4 kvar capacitor or
not at LV side of transformer just after energy meter?
Thank you again and awaiting for ur positive reply soon.
Answer Posted / surya
the 4kvar capacitor improve the pf but you must keep in
mind that installed the capacitor permanentely only at load
time.switched off the capacitor on unload time since i
think at unload time the 4kvar capacitor become a self-load
& increase your electricity bill.
|Is This Answer Correct ?||2 Yes||0 No|
Why efficiency in thermal power plant is low?
how to calculate slip ring induction motor stator and rotor currents??
what type questions asked in hp cl
How to calculate the sag of OPGW during stringing???
why in the three pin plug all 3 pins are cutted ?
WHAT IS ELECTRICAL MAINTAINTENCE ?
what are the types of electromagnetic forces developed in practical transformer?
how to calculate the battery AH
What is an ideal transformer?
how we can set the IDMT relay.
how i chosse capacitor bank if my energy meter is 48 kvr? tell me capacitor bank chossen formula?
how to avoid Saturation in C.T?
What is force on a conductor in a magnetic field ?
how can you calculate fault level ?
what are the possible reaons & remedies if resistance of NGR getting heat up