How to calculate the ups battery back up? give the formula.
Answers were Sorted based on User's Feedback
Answer / ananth
T = N.V.X / VA
T= Time in Hours
N = No. of batteries
V= Voltage of Battery
X= Amp-Hour of the Battery
|Is This Answer Correct ?||156 Yes||29 No|
Answer / subir kumar manna
numbers of battery * ah of battery /output kva*130
0.32 hours .
|Is This Answer Correct ?||93 Yes||48 No|
Answer / bhushan
UPS / Invertor Battery Backup Time =
Batt Voltage X No.of (Batteries) X Ah (Single Battery) /
Total Load (Watts) = No.Hours Backup
Example :- 12v X 20(Batteries) X 200Ah (Single Battery)
/ 6000 (Watts) = No.Hours Backup
48000 / 6000 Watts = 8 Hours Backup
|Is This Answer Correct ?||55 Yes||14 No|
Answer / dhruvendra
|Is This Answer Correct ?||43 Yes||22 No|
Answer / a. dutta
To get one hour battery backup:
BATTERY AH = 1000 × VA × PF /( NO. OF BATTERY × BATTERY
VOLTAGE × LOAD% × PF
|Is This Answer Correct ?||27 Yes||6 No|
Answer / sayyed fayyaz ahmed
Calculating the UPS and Battery Backup Time
Before calculating the Battery Backup, let us know a few
factors that vary battery backup.
For and UPS with 875Va we can us a maximum load of 640
watts 677Va we can us a maximum load of 540 watts
The main thing we should understand is that whatever may be
the UPS wattage the battery backup will not vary.
The battery backup will only vary depending on the battery
Ah and the Usage Load.
To calculate UPS backup, we have a simple formula.
UPS Backup = Battery Ah * (Volts/Load) * (1/Power Factor)
Example: Let us calculate the backup for a system UPS
Load is the usage power, suppose we are running a PC then
the load is around 300 watts
Power Factor varies for device to device, the average power
factor is 1.4
Voltage is the voltage of the battery.
For a single battery the voltage is 12v.
If the batteries are connected in a series Voltage = 12 *
no. of batteries.
Battery Ah is the battery ampere used for the ups,
System UPS battery AH is 7
Then Battery Backup = 7 * (12/300) * (1/1.4)
= 7 * (0.04) * (0.7)
= 0.19 hours
= 11.4 Minutes
Note: You can use the same formula for calculating the
battery backup for home UPS or an INVERTER.
|Is This Answer Correct ?||19 Yes||12 No|
Answer / narayanarao.s
back up( in hours)= system dc volts x AH rating(
battery)/kva(load)x system power factor.
|Is This Answer Correct ?||11 Yes||5 No|
Answer / balajiram
Time=ups efficiency*battery efficiency*battery low volts*battery AH/ups output(watts)
|Is This Answer Correct ?||14 Yes||12 No|
Answer / prabhu
Battery Backup= No.of Batteries X Voltage of the batteries X Capacity of the batteries X Pf (0.8) / Load in Watts
|Is This Answer Correct ?||3 Yes||2 No|
Answer / prakash dhanshetty
backup time=(kva rating*power factor)!dc low of system
|Is This Answer Correct ?||8 Yes||8 No|
What are merits & De-merits of State-Space Method? What is series programming, parallel programming, general programming & direct programming ? And, difference between these programmings Techniques ?
As all us know that the capacitor panel is connected to improve the power factor when it is PF is low. whether we can connect the capacitor panel on D.G. side(? If it is yes means why?
what is the IS foe lightning arrester?
what is meant by phase &line voltage, how its differ from each other ?
What is electrical diversity factor in electrical installations?
why batteries are rated in ampere hour
what is the working principle of electrical generator
what is the uses of C.V.T transformer in switch yard?
WHY RATING OF VCB NOT LESS THAN 630A
why we use taping of transformer on HT side?
is power factor correction related with vector group of transformer i.e:Dyn11?
What is the difference between AC Drive and VFD?