what is pf. how to calculate capacitor bank value to
maintain unity pf.

Answers were Sorted based on User's Feedback

what is pf. how to calculate capacitor bank value to maintain unity pf...

Power Factor is defined as the ratio of Real power and
Apparent power.

for calculating Capacitor bank value the formula is :

kVAr = KW {tan(cos^-1 Phi e) - tan(Cos^-1 Phi d)}

Where - Phi e = existing Power Factor.
Phi d = Desired Power Factor.

 Is This Answer Correct ? 99 Yes 8 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

for calculating Capacitor bank value the formula is :

kVAr = KW {tan(cos^-1 Phi e) - tan(Cos^-1 Phi d)}

Where - Phi e = existing Power Factor.
Phi d = Desired Power Factor.

 Is This Answer Correct ? 42 Yes 8 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

to calculate desired capacitor value, the formula is

KVAR= KW(TAN PHI 1 - TAN PHI 2 )

WHERE PHI 1 = EXISTING POWER FACTOR
PHI 2 = REQUIRED POWER FACTOR

 Is This Answer Correct ? 23 Yes 14 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

KVAR= KW(TAN PHI 1 - TAN PHI 2 )

WHERE PHI 1 = EXISTING POWER FACTOR
PHI 2 = REQUIRED POWER FACTOR

 Is This Answer Correct ? 14 Yes 9 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

Calculation and selection of required capacitor rating
Qc = P * {tan [acos (pf1)] - tan [ acos (pf2)]}
Qc = required capacitor output (kVAr)
pf1 = actual power factor
pf2 = target power factor
P = real power (kW)

 Is This Answer Correct ? 6 Yes 1 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

hi..i also interested in it..i am carrying out pf
measurement system and i am headache in how to maintain the
unity pf too..

 Is This Answer Correct ? 40 Yes 36 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

The correct answer and below is the proof of the formula:

KVAR= KW X [&#8730;(1–(COS&#1060;)^2)]/COS&#1060;

The proof:
Pythagoras Theorem states that in a right-angled triangle
the square of the hypotenuse is equal to the sum of the
squares of the other two sides.
so that:
Q is the hypotenuse.
S is the opposite.
Tan&#1060;= opposite/adjacent = S/P -----> S=P x(Tan&#1060;)
Pythagoras said that:
Q^2= P^2 + S^2
P^2/(COS&#1060;)^2= P^2 + (P^2 x (Tan&#1060;)^2)
by divide P^2:
1/(COS&#1060;)^2 = 1 + (Tan&#1060;)^2
by changing the both sides:
(Tan&#1060;)^2 = (1/(COS&#1060;)^2) - 1
(Tan&#1060;)^2 = (1/(COS&#1060;)^2) - ((COS&#1060;)^2/(COS&#1060;)^2)
by Taking the (1/(COS&#1060;)^2) Common factor:
(Tan&#1060;)^2 = {1/(COS&#1060;)^2)} x ( 1 - (COS&#1060;)^2)
by taking the square root:

Tan&#1060; = [&#8730;(1–(COS&#1060;)^2)]/COS&#1060;

so that:
KVAR = KW x [&#8730;(1–(COS&#1060;)^2)]/COS&#1060;

 Is This Answer Correct ? 5 Yes 1 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

react power kvar=v i sin phi, we know p.f=1,i.e cos phi
calculate sin phi,v i values from total load

 Is This Answer Correct ? 14 Yes 11 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

KVAR= KW(TAN PHI 1 - TAN PHI 2 )

WHERE PHI 1 = EXISTING POWER FACTOR ANGLE i.e., COS^¯1(p.f1)
PHI 2 = REQUIRED POWER FACTOR ANGLE i.e., COS^¯1(p.f2)
p.f 1 = EXISTING POWER FACTOR
p.f 2 = REQUIRED POWER FACTOR

 Is This Answer Correct ? 5 Yes 2 No

what is pf. how to calculate capacitor bank value to maintain unity pf...

The correct answer and below is the proof of the formula:

KVAR= KW X [Sqrt(1–(CosQ)^2)]/CosQ;

The proof:
Pythagoras Theorem states that in a right-angled triangle
the square of the hypotenuse is equal to the sum of the
squares of the other two sides.
so that:
C is the hypotenuse.
S is the opposite.
TanQ= opposite/adjacent = S/P -----> S=P x(TanQ;)
Pythagoras said that:
C^2= P^2 + S^2
P^2/(CosQ)^2= P^2 + (P^2 x (TanQ)^2)
by divide P^2:
1/(CosQ)^2 = 1 + (TanQ)^2
by changing the both sides:
(TanQ)^2 = (1/(CosQ)^2) - 1
(TanQ)^2 = (1/(CosQ)^2) - ((CosQ)^2/(CosQ)^2)
by Taking the (1/(COSQ)^2) Common factor:
(TanQ)^2 = {1/(CosQ)^2)} x ( 1 - (CosQ)^2)
by taking the square root:

TanQ; = [Sqrt(1–(CosQ)^2)]/CosQ;

so that:
KVAR = KW x [Sqrt(1–(CosQ)^2)]/CosQ;

 Is This Answer Correct ? 4 Yes 1 No

More Electrical Engineering Interview Questions

What is the differance between transformer neutral solidly earthed and transformer neutral earthed through resistor?

why electric shock due to dc is dangerous than that of ac

types of central Air conditioner plant?

Why is transformer connect parallel? why not series? ....plz...

What is the diffrence between ofline ups and online ups?

i want to know that what is the eligibility critaria for ongc exam?

why voltage drop will occurs in 3 phase line?

What are the neccessary safety arrangements before commissioning of HV substation?

any one can explain what is the size of pvc,armoured, various sizes of powr cable dia?

What is eddy current & eddy current loss ?

WHAT IS DGA TEST FOR THE TRANSFORMERS.

I decided to provide a 11KV / 440V Xformer in my Substaion. What are the protection required for that?

Categories
• Civil Engineering (4652)
• Mechanical Engineering (3710)
• Electrical Engineering (15818)
• Electronics Communications (2685)
• Chemical Engineering (763)
• Aeronautical Engineering (127)
• Bio Engineering (30)
• Metallurgy (95)
• Industrial Engineering (199)
• Instrumentation (2884)
• Automobile Engineering (171)
• Mechatronics Engineering (74)
• Marine Engineering (103)
• Power Plant Engineering (170)
• Engineering AllOther (1371)