What is the max demand on your transformer and your company?
Answers were Sorted based on User's Feedback
Answer / jatinder dhaliwal
max demand of a company and transformer is the maximum
power that his circuit is likely to draw at any time.
|Is This Answer Correct ?||37 Yes||2 No|
Answer / mohd. karim
i want to give answer of this que. by an Example:
**if connected load of our system( factory,
Works,plant ...Etc) is 1250KW(1.25MW)...it means our maxi
demand at PF 0.83 is 1506KVA (1.506MVA)
one transformer used for this load with rating PF 0.8,
***it means MD in KW is 1200KW
MD in Kva is 1500KVA (1.5MVA)
it means this x-mer is not suitable for this load because
efficiency of x-mer is maxi. at half load. for above
example, this x-mer is suitable for 600KW-850KW at
** is the MD of Company
***is the MD of X-mer
|Is This Answer Correct ?||19 Yes||4 No|
Answer / pablo
The maximum demand of a power transdormer does not exceed
80 percent of its power rating.
|Is This Answer Correct ?||14 Yes||5 No|
Answer / sp singh
Transformer generally selected 25% higher KVA than peak load of the organization.
|Is This Answer Correct ?||1 Yes||0 No|
Answer / will
Maximum demand means that it shall not cross the 100%
rating of the transformer, if the transformer has no
colling stages and can take extra demand.
Normally the cooling stages increase the transformer
capacity to take load 33% more at eact cooling stage.
Ist cooling stage FA-1.33%
2nd cooling stage FA-1.66%
That means when the transformer getting loaded more than
100% capacity the ist cooling stage gets automatically on
and when it gets more than 133% loaded the second cooling
stage gets automatically on.
|Is This Answer Correct ?||4 Yes||9 No|
Answer / rajendran.m
|Is This Answer Correct ?||5 Yes||12 No|
Answer / stanley electrician
Consider that 500kva transformer in your company,
and you use only 250 kva load maximum. you must calculate
the increase of your load for the future five years.
That means, expecting 275 kva load in feuture, you will get
upto 300 kvaon maximum demand.
Simply get 25% extra from the maximum load.
|Is This Answer Correct ?||5 Yes||13 No|
Why transformer ratings in KVA not in KW?
what is the difference between 4pole & 6pole DC Motors & give advantage ?
why capacitor bank shorted by resistance ( 3 terminal )
I have 4 DG set with 1500KVA rating. system breakers are 11KV & alternator are 415 Volts. i want to Know what is max. resistance for body earthing & 415 & 11KV V Neuteal earthing. my fault current is 14 times for 2 sec.
During a temperature rise test of a bus duct, it is fed with 415 volts at 2000 amperes. Why dont we get an electric shock if we touch the bus bars?
how work the differential protection relay in details?
how will reduce the voltage. if 12volt/250ma transformer toreduce 6 volt
Difference between rating factor of cable and derating factor of cable?
Why the transformers making noise?
We have a 62.5 KVA DG with Leyland engine and kirloskar slipring alternator. We have earthed the neutral, and another earthing for the dg body. is it necessary to isolate the dg foundation with rubber pads?
how to select rating of HT Panel
can someone explain that how the speed of the protection system affects the fault level calculation?