What is the max demand on your transformer and your company?
Answers were Sorted based on User's Feedback
Answer / jatinder dhaliwal
max demand of a company and transformer is the maximum
power that his circuit is likely to draw at any time.
|Is This Answer Correct ?||38 Yes||2 No|
Answer / mohd. karim
i want to give answer of this que. by an Example:
**if connected load of our system( factory,
Works,plant ...Etc) is 1250KW(1.25MW)...it means our maxi
demand at PF 0.83 is 1506KVA (1.506MVA)
one transformer used for this load with rating PF 0.8,
***it means MD in KW is 1200KW
MD in Kva is 1500KVA (1.5MVA)
it means this x-mer is not suitable for this load because
efficiency of x-mer is maxi. at half load. for above
example, this x-mer is suitable for 600KW-850KW at
** is the MD of Company
***is the MD of X-mer
|Is This Answer Correct ?||20 Yes||4 No|
Answer / pablo
The maximum demand of a power transdormer does not exceed
80 percent of its power rating.
|Is This Answer Correct ?||14 Yes||5 No|
Answer / sp singh
Transformer generally selected 25% higher KVA than peak load of the organization.
|Is This Answer Correct ?||1 Yes||0 No|
Answer / will
Maximum demand means that it shall not cross the 100%
rating of the transformer, if the transformer has no
colling stages and can take extra demand.
Normally the cooling stages increase the transformer
capacity to take load 33% more at eact cooling stage.
Ist cooling stage FA-1.33%
2nd cooling stage FA-1.66%
That means when the transformer getting loaded more than
100% capacity the ist cooling stage gets automatically on
and when it gets more than 133% loaded the second cooling
stage gets automatically on.
|Is This Answer Correct ?||4 Yes||9 No|
Answer / rajendran.m
|Is This Answer Correct ?||5 Yes||12 No|
Answer / stanley electrician
Consider that 500kva transformer in your company,
and you use only 250 kva load maximum. you must calculate
the increase of your load for the future five years.
That means, expecting 275 kva load in feuture, you will get
upto 300 kvaon maximum demand.
Simply get 25% extra from the maximum load.
|Is This Answer Correct ?||5 Yes||13 No|
Dear Friends, Need your help for connecting APFC panel, Quotation : I have 2 Noâ€™s 1000 KVA Transformers, both transformers are having separate APFC panels, ( Tr-1,400KVAR, TR-2,450 KVAR) Now I want to stop One transformer, present load is 650Amps, Max, So One transformer is enough, I have switched OFF TR-1, but PF is not maintaining properly, its 0.5, So now I want to connect TR-2 APFC also in TR-1 Loads, Can any one answer for my Quotation with drawing, how to connect TR-2 APFC panel in TR-1 Loads,
which IS or IEC is used for earthing,breakdown voltage of transformer oil, hv/pd testing and all type of electrical testing
. What should be the minimum and maximum ohmic value for earthing?
what is 6 pulse and 12 pulse inverter? Explain brifly
how is the cable tray designed & how its total length is calculated for an Industrial plant Say for Ex. (500KW Motor Load)
what is voltage gradient?
What is the difference Marshaling box and RTCC (Relay tap changer circuit) Panel of transformer ?
What are HT & LT Cables? What are their values?
What is class X ct? What rare its uses?
why need to be maintain power factor for industrial customer?
what is formula of illumation calculation
what is the diff.between neutral and earth?