What is the max demand on your transformer and your company?
Answers were Sorted based on User's Feedback
Answer / jatinder dhaliwal
max demand of a company and transformer is the maximum
power that his circuit is likely to draw at any time.
|Is This Answer Correct ?||39 Yes||2 No|
Answer / mohd. karim
i want to give answer of this que. by an Example:
**if connected load of our system( factory,
Works,plant ...Etc) is 1250KW(1.25MW)...it means our maxi
demand at PF 0.83 is 1506KVA (1.506MVA)
one transformer used for this load with rating PF 0.8,
***it means MD in KW is 1200KW
MD in Kva is 1500KVA (1.5MVA)
it means this x-mer is not suitable for this load because
efficiency of x-mer is maxi. at half load. for above
example, this x-mer is suitable for 600KW-850KW at
** is the MD of Company
***is the MD of X-mer
|Is This Answer Correct ?||20 Yes||4 No|
Answer / pablo
The maximum demand of a power transdormer does not exceed
80 percent of its power rating.
|Is This Answer Correct ?||14 Yes||5 No|
Answer / sp singh
Transformer generally selected 25% higher KVA than peak load of the organization.
|Is This Answer Correct ?||2 Yes||0 No|
Answer / will
Maximum demand means that it shall not cross the 100%
rating of the transformer, if the transformer has no
colling stages and can take extra demand.
Normally the cooling stages increase the transformer
capacity to take load 33% more at eact cooling stage.
Ist cooling stage FA-1.33%
2nd cooling stage FA-1.66%
That means when the transformer getting loaded more than
100% capacity the ist cooling stage gets automatically on
and when it gets more than 133% loaded the second cooling
stage gets automatically on.
|Is This Answer Correct ?||4 Yes||9 No|
Answer / rajendran.m
|Is This Answer Correct ?||5 Yes||12 No|
Answer / stanley electrician
Consider that 500kva transformer in your company,
and you use only 250 kva load maximum. you must calculate
the increase of your load for the future five years.
That means, expecting 275 kva load in feuture, you will get
upto 300 kvaon maximum demand.
Simply get 25% extra from the maximum load.
|Is This Answer Correct ?||5 Yes||13 No|
Why Lead-Acid cell voltage is 2.1 volt, why we can not chenged it cell voltage by using extra row-material, only incries its AH.
i have a 1500kVA transformer what is the kWH meter i need to use?
what is the difference between underreach and overreach.what is the advantage of using overreach instead of underreach.explain
What are locations arc protection relay is fixed.
We have given to 3phase supply to ups system & how can coming netural
What is the advantage of AC supply?
Why AC loads wont used in DC input supply? and Why DC loads wont used in AC input supply?
how will calculate the safe starting current of 3-phase squirrel cage induction motor?
its Kva and Kv are same?
How do the synchronizing lamps indicate the correctness of phase sequence between existing and incoming alternators?
In power transformer tappings are provided on A high voltage side B low voltage side C In middle of both the windings D both high and low voltage side
What is the voltage b/w nutral and earth