what is brushless generator.How does work it..??
Answers were Sorted based on User's Feedback
Answer / shiv shankar
the exicter is coupled to the generator shaft. the exciter
carries the permanent magnet gen., ac gen., diode wheel
arrangement for rectification and dc generated is directly
fed to rotor via internal contacts through shaft hole
|Is This Answer Correct ?||10 Yes||0 No|
Normally brushes were used with a commutator with
generators with a rotaring field or sliprings for
As the brushes always would require servicing generator
manufacturers found ways to eliminate them. To do this they
used 2 generators on the same shaft. A small one (exciter)
with a stationary field to produce a 3 phase supply on the
rotor. The output from this generator is rectified with the
rotating diodes and feed into the main rotor. This is a
rotating field generator.
The voltage is controlled by controlling the field of the
small exciter generator. A second benefit is that the field
current is reduced from anywhere between 25 to 100 amps to
only 2 to 10 amps. This makes the control of the field much
easier and cheaper.
|Is This Answer Correct ?||1 Yes||0 No|
Answer / sakthivel perambalur
we know that dynamically induced emf and statically induced emf
|Is This Answer Correct ?||4 Yes||5 No|
what is the principle of servo motor
what is the use of CurrentTransformer in AVR ?
i heard that power factor(PF) is the main concern for industries, if they are maintaining PF around 0.6 they will be fined for that. now the question is, how can they improve the PF ranging between 0.9 to 0.95 which is safe for them i,e escaping from the fine?
i need project topics along with circuit diagram in the electrical and electronics engg and also some websites regarding projets.
Dear All, Pls let me know about ELR.... CBCT is using for singnal purpose... How it works.. any body can explain pls.......
What is the use of bundle conductors?
What is technical difference between ELCB & ELMCB?
what is the suitable voltage of transmission line to transmit 10000w power through 250 km. (a)11kv (b)33kv (c)66kv (d)132kv ]and please tell me whats the logic behind it
Could Please Explain briefly. Why used stabilizing resistance series with High impedance bus differential protection relay.
A TRANSFORMER 440/400V,DELTA/STAR CONNECTED.THE NEUTRAL CONNECTED WITH GROUND CABLE THAT IS DIRECTLY CONNECTED TO THE PANEL,FROM PANEL IT IS CONNECTED EARTH PIT.IS IT RIGHT? IF IT IS RIGHT LEAKAGE CURRENT AFFECTED.SECONDATY IS PROTECTED WITH EARTH LEAKAGE RELAY.
Can motor act as generator (OR) vice versa? explain how does it do please post the answer technically
why is fan rotating slow speed, what is the problem?