why we avoid parallel operation of diesl generator?
Answers were Sorted based on User's Feedback
Answer / goodwhisher
this site is very good for good engineers,please dont spoil
it please,it's no a funny matter.
dont answare if you dont know,please.
|Is This Answer Correct ?||9 Yes||0 No|
Answer / johnson m.c.
1) Potential of both alternators must be equal. Both must
have same output voltage.
2) Phase sequences of both the alternators must be same.
The RYB phases of one alternator must
be connected the RYB phases of the other alternator.
3) Frequency of both the alternators must be equal. If one
alternator is operating at a frequency of 49
Hz and the other one is delivering voltage at 51 Hz, then
load on the second alternator would be
more. We have to increase the speed of the prime mover of
the first alternator in order to effect a
match in frequencies.
4) Phase angle of voltages of the two alternators must not
be more than 10 degrees.
5) During manual operation of synchronization, the load
could witness kick (which is a peak of
current). This kick could burn the alternators on the load.
The only solution is the use of automatic
synchronisation equipment. However, expert engineers could
close the CB of the second
alternator when the difference of phase angle between the
two voltages is 2 degrees.
6) The alternators must share loads with respect to their
7) The alternators must have similar voltage drooping
8) The engines of the alternators must have similar
|Is This Answer Correct ?||10 Yes||4 No|
Answer / rajanikant
lokesh why you want to spoil this site this is very good
site for engineers
|Is This Answer Correct ?||3 Yes||0 No|
Answer / lokesh ranjith
because in parallel operation when electricity fails all Dg
sets will gets on even if the load is less also
There will be more diesel consumption
if we run the dgsetd solo mode we can give 80% load can get
|Is This Answer Correct ?||2 Yes||20 No|
why we use carbon brush in exciter&genrator?
what is the capacitance of a single conductor
what happens if we connect two parallel ideal voltage sources across resistor?what is current flowing through resistor?
we know that dc motors are more superior then three phase induction motors in torque generation though they are not much used in industries why?
Which types of following motors are most efficient?
HOW DOES ONE SELECT A TRANSFORMER PHASOR GROUP IE, WHETHER A STAR-DELTA TR OR A STAR-STAR OR A DELTA-DELTA, ETC. TRANSFORMER IS MORE SUITABLE FOR A PARTICULAR KIND OF LOAD OR WORKING CONDITION???
how many types of ratings are there of transformer
what is the meaning of improving the power factor (give technical ans not therotical)
how to calculate the current if i know power in MW and voltage 11kv/415v and also want to know that incoming cables for trnsformer
what is KA rating and how can we choose switchgears on applications
how we can set the IDMT relay.
what role neutral plays in electrical circuit? If neutral is not there what will be the effect