why we avoid parallel operation of diesl generator?
Answers were Sorted based on User's Feedback
Answer / goodwhisher
this site is very good for good engineers,please dont spoil
it please,it's no a funny matter.
dont answare if you dont know,please.
|Is This Answer Correct ?||9 Yes||0 No|
Answer / johnson m.c.
1) Potential of both alternators must be equal. Both must
have same output voltage.
2) Phase sequences of both the alternators must be same.
The RYB phases of one alternator must
be connected the RYB phases of the other alternator.
3) Frequency of both the alternators must be equal. If one
alternator is operating at a frequency of 49
Hz and the other one is delivering voltage at 51 Hz, then
load on the second alternator would be
more. We have to increase the speed of the prime mover of
the first alternator in order to effect a
match in frequencies.
4) Phase angle of voltages of the two alternators must not
be more than 10 degrees.
5) During manual operation of synchronization, the load
could witness kick (which is a peak of
current). This kick could burn the alternators on the load.
The only solution is the use of automatic
synchronisation equipment. However, expert engineers could
close the CB of the second
alternator when the difference of phase angle between the
two voltages is 2 degrees.
6) The alternators must share loads with respect to their
7) The alternators must have similar voltage drooping
8) The engines of the alternators must have similar
|Is This Answer Correct ?||10 Yes||4 No|
Answer / rajanikant
lokesh why you want to spoil this site this is very good
site for engineers
|Is This Answer Correct ?||3 Yes||0 No|
Answer / lokesh ranjith
because in parallel operation when electricity fails all Dg
sets will gets on even if the load is less also
There will be more diesel consumption
if we run the dgsetd solo mode we can give 80% load can get
|Is This Answer Correct ?||2 Yes||20 No|
What is the difference between Neutral and Eatrh?
why the impedence of the transformer is expressed in percentage?
electricity board have asked me what size meter i need fitted in my garage, its a 415volt supply and i want to run six 20amp supplies tolifts and things plus ten florry lights , what kva meter do i need??
what happen as when voltage drop(or may decrease) ? in case of atomic base theory?
How to find the maximum load, that can be supplied by a transformer.....
WHAT IS START TO INDUCTION MOTER IN STAR TO DELTA OF >5HP ?
CAN ANYBODY EXPLAIN WHAT ACTUALLY MEAN BY THE PHASE DEFFRENCE? R,L,C CIRCUITS?
why power not passes in plastic and rubber material
if we look on phasor of the transformer vaoltage is 180 oppsite at primary and the secondary so to improve a power factor is secondary should kept negative to improve it primary side means is -.90 became +.90 at other side
what are check points to be checked while charging switchyard?(CT,PT,BREAKER,POWER TRANSFORMER)
how to calculate total load in a villa?
if we have to design a small transformer of rating 1 kva or 1 mva , how can we design it?