why we avoid parallel operation of diesl generator?
Answers were Sorted based on User's Feedback
Answer / goodwhisher
this site is very good for good engineers,please dont spoil
it please,it's no a funny matter.
dont answare if you dont know,please.
|Is This Answer Correct ?||9 Yes||0 No|
Answer / johnson m.c.
1) Potential of both alternators must be equal. Both must
have same output voltage.
2) Phase sequences of both the alternators must be same.
The RYB phases of one alternator must
be connected the RYB phases of the other alternator.
3) Frequency of both the alternators must be equal. If one
alternator is operating at a frequency of 49
Hz and the other one is delivering voltage at 51 Hz, then
load on the second alternator would be
more. We have to increase the speed of the prime mover of
the first alternator in order to effect a
match in frequencies.
4) Phase angle of voltages of the two alternators must not
be more than 10 degrees.
5) During manual operation of synchronization, the load
could witness kick (which is a peak of
current). This kick could burn the alternators on the load.
The only solution is the use of automatic
synchronisation equipment. However, expert engineers could
close the CB of the second
alternator when the difference of phase angle between the
two voltages is 2 degrees.
6) The alternators must share loads with respect to their
7) The alternators must have similar voltage drooping
8) The engines of the alternators must have similar
|Is This Answer Correct ?||10 Yes||4 No|
Answer / rajanikant
lokesh why you want to spoil this site this is very good
site for engineers
|Is This Answer Correct ?||3 Yes||0 No|
Answer / lokesh ranjith
because in parallel operation when electricity fails all Dg
sets will gets on even if the load is less also
There will be more diesel consumption
if we run the dgsetd solo mode we can give 80% load can get
|Is This Answer Correct ?||2 Yes||20 No|
why is that a 4*4mm cable,is always powdered internally
if we have 320KVA Genset kindly advice how much load we can put it.
Whether the vacuum contactor requires Short circuit protection?If No,why?
plz send me HPCL apptitude paper.. email@example.com
y we are used signal conditioner in capacitive transducer
How can calculate ups battery back up time?
How do i carry out or know the vector group of a Dyn1 and Dyn5 transformer
I try to check the three phase voltage in multimeter, in 125A isolator switch incommer. first i touch R phase, and then i touch Y phase using multimeter, the moment i touched, it blasts and that moment i got blindness. multimeter selector position is correct(750V AC MODE AND RED PROBE WASS IN v AND BLACK PROBE WASS IN COM. MODE. COULD ANYBODY GIVE ANSWER FOR THIS TO AVOID FURTHER ACCIDENTS PLEASE?
In a Circuit how the MCB and Fuse ratings are calculated. And shall the fuse follws the MCB or it is otherwise?
why normally Generator rating are between 11Kv to 22Kv?
control & auxilary circuits used for circuir breakers
can we run a motor rated 50Hz,415vac,1440RPM At higher speed then rated on name plate with the help of VFD /drive on long term basis.wheater it will effect the motor life