Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

How to calculate the current carrying capacity of
electrical cables

Answers were Sorted based on User's Feedback

How to calculate the current carrying capacity of electrical cables..

current carrying capacity of the conductor is depend on
size of cable and current density of used material of cable
conductor

current carring capacity= size of conductor/current density
of materils

 Is This Answer Correct ? 157 Yes 55 No

How to calculate the current carrying capacity of electrical cables..

Current carrying capacity = FLC / DF
To refer cable catelouge choose the cable sizes
-Derating factor (DF) =0.72
-Full load current (I)= P / (1.732 x V x P.F)

 Is This Answer Correct ? 122 Yes 40 No

How to calculate the current carrying capacity of electrical cables..

For calculate the current carrying capacity.
First we should calculate the cross section area of the
conductor (sq.mm) and conductor material used in cable.

Each and every matals are having its own current carring
capacity. This table is avail at IS.

Current carring capacity may reduce by some other factors
like the cable length and insulation's heat withstandable
capacity.

 Is This Answer Correct ? 101 Yes 28 No

How to calculate the current carrying capacity of electrical cables..

There is no need to calculate ampacity of the cable it would
be provided by the manufacturer its self or else if you want
to calculate it by your self you should also know its
specific resistivity,working temp,core dia & insulation
thickness.

 Is This Answer Correct ? 134 Yes 81 No

How to calculate the current carrying capacity of electrical cables..

The current carrying capacity of a cable is called
Ampacity. For the porpose of the above calculation there
are some concepts that must be taken in consideration .
like Dia,Insulation material and thickness,type of conductor
(Copper/Aluminium),Resistivity and the working conditions.
the "Recommended Cable Sizes and their load capacity as per
Rating Cu Al
10A 1.5MM2 1.5MM2
15A 2.5MM2 2.5MM2
20A 2.5MM2 4.0MM2
25A 4MM2 6MM2

 Is This Answer Correct ? 89 Yes 36 No

How to calculate the current carrying capacity of electrical cables..

Actually current carrying capacity of the cable we can from
the manufacturer, But for the referance purpose I can give
some idea about current capacity of the cable.
So generally we are using two types of cable i.e,. copper &
Aluminium.
copper is the best conductor than the aluminium
At 1Sqmm copper conductor will Approx 2 amp in ground
At 1Sqmm copper conductor will Approx 2.4 amp in air
At 1Sqmm Aluminium conductor will Approx 1.2 amp in ground
At 1Sqmm Aluminium conductor will Approx 1.6 amp in air.

For example:
p=50kw
So
for aluminum cable size(air)= load current/1.6
=87/1.2
=72.5
But In the market there is no availability for 72.5 Sqmm so
we can propose 70Sqmm or 95Sqmm.
This is the one of the best procedure for for cable
selection with using catelogues

 Is This Answer Correct ? 81 Yes 36 No

How to calculate the current carrying capacity of electrical cables..

It depends on many factors.

1. Material - Copper/ Aluminum
2. Voltage Class - Some volts to 765 KV
3. AC/ DC
4. Type of Insulation
5. Most Importantly - Cable Cross-section Area

Refer IEC-60183 for detailed guide

 Is This Answer Correct ? 52 Yes 19 No

How to calculate the current carrying capacity of electrical cables..

Refer IEC 287.If you want me to calculate the same. i will
do it for you

 Is This Answer Correct ? 35 Yes 21 No

How to calculate the current carrying capacity of electrical cables..

hi frnd.. what will u say for the given ques. if interviewer asked, How a manufacturer determines the current carrying capacity of electrical cables??

 Is This Answer Correct ? 8 Yes 5 No

How to calculate the current carrying capacity of electrical cables..

Well, First try to calculate the total load of the system.
For example total load is 1000KW. The current can be
calculated as P=1.732VICOS(PHI). Hence total current will
be 1732A by considering V=415volt, power factor=0.8.

Step2: To calculate the cable size

Vd = mV/L/A

where Vd= Allowable voltage drop which is normally 2.5
percentage to 4 percent.
L = Lenght of the cable from the source to feeder
A = Ampere rating

Let us consider L = 1000Meters
A = 1732A
Vd = 2.5 percentage of 415V as in U.A.E.
= 2.5*415/100 = 10.375

Use these value in the above formula

mV= Vd/L*A
= 10.375/1000*1732
= 0.005 volt

Refer to the cable catalogue in your region and find out
the current carrying capacity of the cable which will be
totally depend upon the atmospheric condition, in cold
place a smaller diameter of cable can carry larger current
and in hot areas the same size will carry lesser current.

In U.A.E. we are normally using 11x1c 630sqmm cable with
2500A incomer breaker. But cross check the voltage drop as
calculated above is within the limit of voltage drop of
these cables else you have to go to higher size of cable
untill the voltage drop met the design milli volt drop of
the cable.

 Is This Answer Correct ? 14 Yes 12 No

More Electrical Engineering Interview Questions

What is Cement

State Maximum Power Transfer theorem.

can we calculate the diameter of the cable by its cross section?

Why transmission line carryiny high voltage and low current?

what is the method of earthing of a transformer using electrodes?

HT/LT TRANSFORMER TEST?

What is notching in dc machine?

Why phase sequence ryb called colours.

why to need a electrical earthing?

What is kirchoff ’s current law (kcl)?

Why TAP changer provided in primary side of HT transformer ? and why not in secondary?

how many parameters can integrate with fire alarm basically ?

Categories
• Civil Engineering (5081)
• Mechanical Engineering (4448)
• Electrical Engineering (16620)
• Electronics Communications (3915)
• Chemical Engineering (1093)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2994)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (171)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1379)