HAI,HOW TO SET THERMAL OVERLOAD RELAY FOR DOL STATRTER
FEEDER AT START AND RUNNING?
Answers were Sorted based on User's Feedback
Answer / fairos
First, for thermal overload relay has no meaning in term of setting it while on running or starting. It purely based on rated current of the motor.
when you look at the nameplate of the motor there should be a data that mention "duty" which normally either 1, 1.1 or 1.2 in value. If the duty is 1 then you can only set the overload relay at 100% of the rated current. If duty is 1.1 then the motor is allowed to operated at 10% higher than it rated current hence you can set your relay at 110% of rated.
Generally people would set at 10-15% higher than rated current. But sometimes being conservative is okay, which you can set the relay below the rated current. This can be done as long as it is not tripping unnecessarily.
|Is This Answer Correct ?||22 Yes||3 No|
Answer / vilas
First take a current of each phase with tong tester,while
running on normal load,
Then set the over load accordding to the load slightly
higer than normal running current, care should be taken
that it should not be more than rated current which is
always mentioned on the motor name-plate.
|Is This Answer Correct ?||7 Yes||7 No|
Answer / pankaj sharma
Set the relay to motor full load current as mention on motor plate
|Is This Answer Correct ?||5 Yes||5 No|
Answer / mohit
set thermal overal relay to 95% of full load current of
|Is This Answer Correct ?||6 Yes||20 No|
i installed 100kva ups. what KVA genset they should provid in input side? plz any update formula or ans with reason.
Let me know that how i calculate the alternator sub tranciant reactance and tranciant reactance.
What is GNR ? How much value of ground neutral resistance?
Can anyone explain me about the RLC based Impulse high voltage generator and how to and operation of Series resonant High voltage reactor...?
Two 11 kv lines are feeding to common bus in a substation,I have one set of CT & PT(3ct,2pt), How can I measure both lines power using single set.
What is meant by bus bar protection?
what is the difference between delta delta and star delta connection transformer? why we use delta delta transformer since it need earthing transformer for grounding?
in short circuit. test of a transformer 5 to 10% ofvrated voltage is used why??? if we use rated voltafe then what will be?
what is "pu" in electrical engg.
What is difference between dc three point starter and dc four point starter?
why do we use 25kv supply for traction purpose
Can any one help me how to set an overload set the range from 2.8A to 4A , rated motor current 22A, CT 60/5A