what is the difference between cable routing and scheduling?
Answers were Sorted based on User's Feedback
Answer / victorvgp
In general cable routing doc. shows inf. about how cables
are routed in cable trays, trenches and duct banks.
Whereas, cable schedule shows inf. about the specification
of cables along with the inf. listed at the end.
cable routing - cable routing cross section layout (or)
cable routing layout
In cable routing cross section layout, cross section of a
particular [DBE(Electrical Duct Bank)/CTE(Electrical Cable
Trench)] is showned, which shows the actual dimensions of
DBE/CTE and how the cables are arranged as per the type
(LV/MV), requirement and sequence.
Cable shedule is of two types one is Internal Cable
Schedule and External Cable Schedule.
In this doc. inf. of cables run inside the
substations such as Transformer to Busbar, Busbar to Switch
board like that.,
In this doc. inf. of cables run outside the
substation such as from Switch board to LDB, Switch board
to Equipment/LCS like that.,
The following inf. are available in cable schedule:
1. Cable id no.
2. From which equipment/SB
3. To which equipment/SB
4. Substation No.
5. Unit no.
6. Cable type(cu/xlpe/swa)
7. Cable voltage[.6/1]or[3.6/6(7.2)]
8. Remarks(inf. about work nature of cable) etc.,
|Is This Answer Correct ?||34 Yes||1 No|
Answer / udayak25
s, Victor is 100% correct.
in short -
cable routing is a drawing which shows how cables are to be
cable schedule document shows the cable specifications like-
resistance, cumulative resistance, length, terminations etc.
|Is This Answer Correct ?||5 Yes||0 No|
Answer / suni
Victorvgp good answer
Do u know when connector is used both end how cabel is
if U KNOW MAIL to firstname.lastname@example.org
|Is This Answer Correct ?||4 Yes||2 No|
Answer / purushothaman.m
|Is This Answer Correct ?||4 Yes||3 No|
How a ship getting grounded
How does "OUT OF STEP" relay ,for Synchronous motor protection, work?
why DG,Transformer,UPS capacity will be tell in KVA but not in KW?
in a silicon diode we can measure .7v in a voltmeter.but why we can't use this voltage for using?
Proviiding the Dedicated N earth and individual Body Earths ,Finally these all looped /Now my Question :- will it not harm in case of Transformer Fault current flows in Dediacted N Earthing to Looped Body Earthing.
whatis knee point ?
How can calculate thermal overload in relay?
What is the difference between an ELCB and a RCD?
what is relation between ct and pt ratio with multiplication factor of a energy meter? is there any other factor on which multification factor depend?
what is used root two in single phase line?
What are the different types of cable jointing methods for HT and LT power cable?
what is motor capacity of 80TR chiller? and also say what is the formula related temperature, motor capacity, TR?