why 4-20 mA signal is preferred over a 0-10V signal

Answers were Sorted based on User's Feedback

why 4-20 mA signal is preferred over a 0-10V signal..

the signal are transmitted from the field to the
controlroom and vseversa through cables. for long
transmission the cable resistance increases.thus if 0-10v
are transmitted over this long distance,due to the
resistance of cable there will be drop in the voltage and
the signal received at the controlroom will not be
accurate. to overcome this difficulty 4-20ma signal is used
for transmission.

 Is This Answer Correct ? 286 Yes 24 No

why 4-20 mA signal is preferred over a 0-10V signal..

4-20mA :-
1. Easy to find the open circuit.
2. Less noise interference.
3. Current measures remain same in any point of the signal
line.

0-10V :-
This not able to fulfill the above criteria.

So that 4-20mA is preferred over 0-10v

 Is This Answer Correct ? 115 Yes 10 No

why 4-20 mA signal is preferred over a 0-10V signal..

If 0-10 mA is used instead of 4-20mA then there will be
difficulties in error detection.Such as if there is any
fault is the transmission lines..we will never know,wheather
the indicated 0mA current corresponds to the initial
value(calibrated) of the measurement or it is due to fault
in transmission lines.

 Is This Answer Correct ? 120 Yes 24 No

why 4-20 mA signal is preferred over a 0-10V signal..

0-10V :-
1. Voltage droup occurs.
2. Not able to find open circuit(Normally the circuit in
open condition o/p is "0", In 0-10V signal level starts
from 0V itself, so that can not able to find open circuit
easily)
3. Noise interference is high.

4-20mA :-
1. Easy to find the open circuit(because this signal level
starts from 4mA, if the circuit in open the output shows
0mA, so we can find easily the open circuit) .
2. Less noise interference.
3. Current measures remain same in any point of the signal
line.

So that 4-20mA is preferred over 0-10v

 Is This Answer Correct ? 86 Yes 7 No

why 4-20 mA signal is preferred over a 0-10V signal..

Voltage drops due to Resistance and so we are using 4-20 mA

 Is This Answer Correct ? 77 Yes 11 No

why 4-20 mA signal is preferred over a 0-10V signal..

In case of voltage transmission(here 0-10V)
1.there will be voltage drop along the transmission wire.
2.if we use 0 volt then we will be unable to find whether
the obtained 0 volt output is really the system output or
its due to instrument error.So for "live zero" concept we
need to give a particular value(other than zero) in the
lower range value.
3.Capacitive and magnetic effect due to voltage
transmission will be more than that in case of current
transmission.
4.2-wire transmission is not compatible with voltage
transmission.

But in case of 4-20 mA signal the above problems are solved.
1.In series transmission same current flows through the
ckt.So no current drop occurs.
2.Here the lower range value is 4 mA.So we can easily
detect after looking at the o/p whether the instrument
error occurs or not.In case of instrument error zero
3.2-wire transmission is compatible with it.

 Is This Answer Correct ? 52 Yes 5 No

why 4-20 mA signal is preferred over a 0-10V signal..

In industry, the distance from controlroom
and the field is too long. If we use 0-10v signal
for feedback means voltagedrop will occur because of the
resistivity. So, 4-20mA is preferred instand of 0-10v
signal.

 Is This Answer Correct ? 27 Yes 5 No

why 4-20 mA signal is preferred over a 0-10V signal..

in 4- 20
we can find if the process variables give zero because zero
is indicate 4ma
but in 0 - 10 if the process give zero we can not know
because the signal also 0v

 Is This Answer Correct ? 22 Yes 11 No

why 4-20 mA signal is preferred over a 0-10V signal..

4-20mA can be easily detected for find a minimum and maximum
level measurement. in in 0-10 V some noise if we are not
prepared measurement

 Is This Answer Correct ? 9 Yes 5 No

why 4-20 mA signal is preferred over a 0-10V signal..

To troubleshoot the loop or transmission signals,if voltage
signals is used it is difficult to troubleshoot due to it's
non linear properties as well as it's voltage drop within
the transmission,but due to linear current properties it is
easy to troubleshoot the transmission signal or 4-20 mA
signal.
Due to this the 4-20 mA is used in signal transmission.

 Is This Answer Correct ? 4 Yes 0 No

More Instrumentation Interview Questions

A DP transmitter is used to measure the level of an open tank. The drain line of the tank is connected to a control valve, and is configured as, if the level of the tank is 90% the valve should get open 10%. And if the tank level is 10%, the valve should get open 90%. Draw wiring diagram and explain how to configure DP transmitter and control valve using HART communicator. If the span error at output is 1%, what will be the %opening of the control valve at 60% level of the tank?

how feedback signal frm rtd can be use for 2 purpose, i.e. 1for local monitoring and 2nd for controlling in dcs.so how many wired RTD can be used

i m passed my engineering in 2010 in instrumentation and control engineering. my question is can i apply for software jobs or vacancies.??????????? plz give me answer soonnn......

Sir, my yokugava FF TYPE LEVEL transmitter us bad, i don't have spares available, i want to replace it with a Rosemount FF transmitter, please tell me what procedure to be followed and what changes to be done in dcs part.

With N nodes and B branches what will have a network ???

-/5A. What is the meaning and limitations of this in energy meter constant. It is a 3 phase LT Energy Meter. If this Energy Meter is connected through a CT of ratio 200/5 Amps, then what is the multiplying constant and how its will be calculated.

Explain the functions of the CPU of a PLC.

Explain about safety integrated level protection? . How it was differ from other protections ?

selection of the zener barrier for the hazardeous area zone 0

draw the characteristics of chebyshev filter

Is Hart communicator calibration device or communicating device for transmitter?

please send the drdo exam paper

Categories
• Civil Engineering (5069)
• Mechanical Engineering (4437)
• Electrical Engineering (16573)
• Electronics Communications (3915)
• Chemical Engineering (1091)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2984)
• Automobile Engineering (332)
• Mechatronics Engineering (96)
• Marine Engineering (122)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1376)