For 160kw motor what size of cable and material is needed.?
Answer / dayasagar
for star delta starter the thump rule is cable sizing to be 2 X motor KW ie 160 kw motor require 160 sq mm since 160 sq mm is standard size it is better to go for 185 sq mm this rule applies for all star delta motors. here you can go for higher size
for DOL or VFD driven motors 2 time the KW ie 320 sq mm is required since 320 sqmm is not standard size it is better to go for 300 sq mm here you can go at lower size
|Is This Answer Correct ?||0 Yes||0 No|
Are you connected Transformer neutral eathing with it's body earthing or earthing met of switch yard.? Yes or No ? why ?
1.Why we use choke?If we use for high starting voltage then different type choke gives different voltage. Is it correct?
why does rotor rotets?
What is the procedure/activities to be taken to inject the current more than 2000A by using 2000A Loading Transformer?
In a Dyn11 transformer, how are the 3 windings of the delta connected? Assume that R1-R2, Y1-Y2, B1-B2 are the 3 windings on the HV side.
when u are given a timer,push buttons and contactor, how do i practically make a star delta control circuit and a direct online control circuit?
how dc load convert to ac load
In the N-series schneider reclosers. What is the difference between current during fault time and current at tripping? This appears in the Event log in an event of a trip out.
we all know that both the generator and motor are electromechanical conversion devices.....then why we rate motor in kw and generator in kva????
house wiring - series wiring or parallel wiring
What is the earth treantment procedure?
some practicle study shows that the reactive power at the receiving end is not equal to the reactive power at the sending end.But according to theory the reactive power is exchanged by different parts of the network – capacitors and reactors permanently, but is never consumed or produced. Then Where that reacrtive power loss occuring?is there any formula to calculate reactive power loss?