Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

How to find earthfault location in long cable layed
underground or outside.

Answers were Sorted based on User's Feedback

How to find earthfault location in long cable layed underground or outside...

There is an equipment to locate fault ,or you have to resort to loop test

 Is This Answer Correct ? 2 Yes 1 No

How to find earthfault location in long cable layed underground or outside...

You can find the faulted location with the help of multimeter.

Measure the capacitance at both the ends,between faulted
phase with respect to earth.
For one end if it is C1 and for other end it is C2. And
total length of cable is L and Capacitance is C.

Then by using the below formula, you can find the faulted
location

LC=L1c1+L2c2

 Is This Answer Correct ? 2 Yes 1 No

How to find earthfault location in long cable layed underground or outside...

transverse nature of waves is utilised to find the location of fault.when a high dc voltage is superimposed on a signal it becomes a wave. now this wave is given a velocity of 67.5meters/microseconds for 11kv cable and 80 meters/microseconds for 33 kv cables. at the open end the voltage is doubled and the wave is reflected .the time taken by this wave to reach the source is noted and the distance is calculated.

 Is This Answer Correct ? 1 Yes 0 No

More Electrical Engineering Interview Questions

What are IR values and what it should be for coil and for insulator

what is mean by hvdc transmission technology .what is principle of hvdc transmission and technic of hvddc transmission .

how would you determin the horsepower of a motor without a nameplate

Trafo ratio is 11kV/6.6kv,Vector group is YND11. What will be the effect if secondary is used for earthed system.

how many units consumed by 8.5 ton ductable split ac in one hour in 3 phase?

what should be the acceptrd value of winding resistance for 2.5MVA transformer

what are the different methods for the starting of a synchronous motor.

If We are converting the SINGLE PHASE AC into THREE PHASE AC by using STATIC CONVERTERS , then How do we bring the frequency to 50 hz??

why we take movement of rotor always in counter-clockwise direction in 3-phase induction motors?

During the troubleshooting of an inoperative shunt generator, you found the voltage to be 2+ volts; what is known from this. Is it (1). odds are the armature is good (2). odds are there is no field current flowing in field windings (3). odds are the armature is bad (4). both 1 & 2 are correct (5). both 2 & 3 are correct

if earthing is used in place of neutral how the circuit completd.

Why frequency changes due to load variation in power system ? i.e why when load increases frequency decreases?

Categories
• Civil Engineering (5081)
• Mechanical Engineering (4448)
• Electrical Engineering (16620)
• Electronics Communications (3915)
• Chemical Engineering (1093)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2994)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (171)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1379)