I have a question, I visit 01 site and face a problem,
there is 2.5 ton Air Con working, when air con compressor
is running at that time rectifier voltages are increasing
upto 290-295 v and rectifier is giving main high alarm
(rectifier is APC single phase, before starting compressor
rectifier voltages was 230v. when air con is going off
rectifier voltages are decreasing smoothly at its actual
Load on Genset phases is this: Red-13.5 amp AC (Air Con
load), Yellow-1.7 amp AC (BTS lights etc.) and Blew-4 amp
AC (telecom system load),
Genset phase to phase and neutral to phase voltages are
These are 10 sites having same system and same rectifier
APC brand at every site 02 genset are working but the
problem is same at all these 10 sites.
What will be the reason behind???
I want to know what must the CT ratio be on a load of 300A is a 3PH nutral to earh installation?
what is Harmonic effect?
description about dry type transformers
How to improve fuel cell in a distribution system?
How many earthings are required for motors?
The transmission does not have options: a)Partition noise b) Flicker noise c) resistance d) Short noise and reason
how much air gap in induction motor as per the Indian standards?
how to calculate the multiplication factor in HT incomer trivector meters
what is 400kv doble circuit quadpole tower?
what is smartµ grid technology?under coal gassification?
what is star&delta connections?