is it possible to flow a current between nutral and earth
in a circuit? although nutral and earth having same
if any body now any solid reason because i am getting a
triping problem in rcbo due to nutral and earth shorting???
Answers were Sorted based on User's Feedback
The reason you are getting tripping of the RCBO is the way
the RCBO works.
The RCBO senses the current in the phase and neutral. As
long as these are balanced it will not trip. It is designed
to trip if there is an inbalance. This is usually a current
flow between the phase and earth which is then not returned
by way of the neutral.
When the is a short between the earth and the neutral it
provides a parallel circuit. Some of the current will flow
through the earth and some through the neutral as they are
now connected together on both sides of the RCBO. The RCBO
senses an inbalance because not all of the phase current is
flowing back thriough the neutral and it therefore trips.
|Is This Answer Correct ?||0 Yes||0 No|
Answer / k.prakashchandra
If there is a loose connection in the neutral wire ,neutral
point gets shifted to the point of loose connection at the
incoming.Then there will be some voltage in the neutral wire
beyond it, resulting in flow of current when in contact with
the earth wire.
|Is This Answer Correct ?||0 Yes||1 No|
How can I calculate per unit (KWH) fuel (Gas/ Diesel both) consumption 1MW unit?
what is the MF if CT ratio is 500/5 and in meter specification is 3.75 REVS/KWH? Thanks and Regards Selvendran.N
If one ct is reversely connected in Y system what will effect in kwh and kvarh meter?
how to find ratio of CT & PT in 66/11kv 12 mva supply system ? explain with calculation.
What are the advantages of using distance protection schemes as opposed to normal overcurrent/ earth fault protection on high voltage feeders.
Why we are testing a tan delta test in transformer? which purpose conduting that test? and time priode test?
For my plant the electricity department charging some amount for t/f losses. May i know what are transformer losses
What is meant by vector group
As per BIS, Earth pit resistence value?
How can determine cable size with respect to cable length and area in mm2
which motor is used in mixies
why secondary of transformer always grouded?