How to calibrate a orifice differential pressure flow
transmitter in process?
Answer / ayaz
first communicate ccr tag conform and turn MOS if required
when 5 way manifold
1 hp side close
2 equalizer open
3 lp side close
and then hp and lp drain or vent should be open
the transmitter will show zero if not calibrate it
first adjust the zero
2nd second span check and adjust
and then service
1 drain or vent close
2 equalizer close
3 and then hp side open and lp side open
|Is This Answer Correct ?||2 Yes||0 No|
What is the exact differences between HART,FOUNDATION FIELDBUS,PROFIBUS?
when we are using HART COMMUNICATOR why we are using 250 ohm resistance while using HART COMMUNICATOR.
basic connection and principle of axial shift sensor n differential sensors in tubine describes n draw......
what happens when the profibus fails while in operation (operation of a valve)?
without color coding, without nameplate, without multimeter how can you find the type of thermocouple???
what is plc?
where i can get training in INTOOLS and PDMS in Delhi-NCR OR north part of India. please reply with ur ans. at firstname.lastname@example.org
What is the purpose of the analyzer in petrochemical plant?
please tell me what is a light up procedure of Cfbc boiler and what it's axuillaries of cfbc boiler?
Draw symbols of the following :
How to measure Flow of air line,what is the procedure of creating DP in line to measure Flow!
please tel me the calibration of pneumatic controler.