Answers were Sorted based on User's Feedback
Answer / vimal m
Transformer Ratio Test
The performance of a transformer largely depends upon perfection of specific turns or voltage ratio of transformer. So transformer ration test is an essential type test of transformer. The voltage should be applied only in the high voltage winding in order to avoid unsafe voltage.
Procedure of Transformer Ratio Test
First, the tap changer of transformer is kept in the lowest position and LV terminals are kept open.
Then apply 3-phase 415 V supply on HV terminals. Measure the voltages applied on each phase (Phase-phase) on HV and induced voltages at LV terminals simultaneously.
After measuring the voltages at HV and LV terminals, the tap changer of transformer should be raised by one position and repeat test.
Repeat the same for each of the tap position separately.
The above transformer ratio test can also be performed by portable transformer turns ratio (TTR) meter. They have an in built power supply, with the voltages commonly used being very low, such as 8-10 V and 50 Hz. The HV and LV windings of one phase of a transformer are connected to the instrument, and the internal bridge elements are varied to produce a null indication on the detector.
|Is This Answer Correct ?||0 Yes||0 No|
is it necessary to earth the rmu before cutting off the transformer winding?if yes why?
can any one explain me the where is the use of plc and scada
why transformer rating in KVA or MVA instead of KW n MW??
two phases with neutral supply can be taken in 3C X 10 sq.mm cable .
Can any body describe me why a soft starter is used for 6.6kv induction motor instead of VFD ?
how digital four pin earth resistance tester works
A 60W,250V bulb when connected to a 230V supply will it give more light or less or will be give normal light?
why we use Test Terminal Block in 11 KV and 33 KV electrical panels.
Is the installation of the filter cloths necessary before spreading the gravels at the transformer yards?
what sq.mm copper pvc wire need for ac load current 25amps for 230v ?
carbon zinc cell voltage?
What is the In door to Out door Sub Station.