Answers were Sorted based on User's Feedback
Answer / vimal m
Transformer Ratio Test
The performance of a transformer largely depends upon perfection of specific turns or voltage ratio of transformer. So transformer ration test is an essential type test of transformer. The voltage should be applied only in the high voltage winding in order to avoid unsafe voltage.
Procedure of Transformer Ratio Test
First, the tap changer of transformer is kept in the lowest position and LV terminals are kept open.
Then apply 3-phase 415 V supply on HV terminals. Measure the voltages applied on each phase (Phase-phase) on HV and induced voltages at LV terminals simultaneously.
After measuring the voltages at HV and LV terminals, the tap changer of transformer should be raised by one position and repeat test.
Repeat the same for each of the tap position separately.
The above transformer ratio test can also be performed by portable transformer turns ratio (TTR) meter. They have an in built power supply, with the voltages commonly used being very low, such as 8-10 V and 50 Hz. The HV and LV windings of one phase of a transformer are connected to the instrument, and the internal bridge elements are varied to produce a null indication on the detector.
|Is This Answer Correct ?||0 Yes||0 No|
why humming sound occured in h HT transmission line
why AC signals are represented by sinusoidal waveform?WHY other waveforms not used for representation
Can Induction motor run at over rated speed? ( 15oo rpm is rated speed for 50HZ. is it possible to ride 3000 RPM with same motor with the help of VVVFD for continues ride of 100HZ)
Abb 11kv how it is closing automatically when the cb is racking in and rack out when it reaching test position
what is DAR test?
why we are using large cross section cable at load side and small at other (11kv to trsfr)side of transformer? when the load increses current at both side increases,right?
pls define kvarh
In how we connect watt meter for open & short circuit test of a single phase transformer.
In an ACB shunt trip coil and undervoltage coil operated normally( breaker open and charged). But closing coil not operating untill manually discharge and recharging. Any help.
ct connection of energy meter
An 8 pole, 50 Hz, 3-phase IM is loaded to a poing where pull out torque will occur. The rotor resistance per phase is 0.3 ohm and motor stalls at 650 rpm. The rotor frequency at maximum torque point is A 3.33% B 4.44% C 5.55% D 6.66%
Transformer Parallel Operations