Answers were Sorted based on User's Feedback
Answer / vimal m
Transformer Ratio Test
The performance of a transformer largely depends upon perfection of specific turns or voltage ratio of transformer. So transformer ration test is an essential type test of transformer. The voltage should be applied only in the high voltage winding in order to avoid unsafe voltage.
Procedure of Transformer Ratio Test
First, the tap changer of transformer is kept in the lowest position and LV terminals are kept open.
Then apply 3-phase 415 V supply on HV terminals. Measure the voltages applied on each phase (Phase-phase) on HV and induced voltages at LV terminals simultaneously.
After measuring the voltages at HV and LV terminals, the tap changer of transformer should be raised by one position and repeat test.
Repeat the same for each of the tap position separately.
The above transformer ratio test can also be performed by portable transformer turns ratio (TTR) meter. They have an in built power supply, with the voltages commonly used being very low, such as 8-10 V and 50 Hz. The HV and LV windings of one phase of a transformer are connected to the instrument, and the internal bridge elements are varied to produce a null indication on the detector.
|Is This Answer Correct ?||0 Yes||0 No|
How many double suspension hardware fittings are required on a double circuit transmission tower?
Application of DC motors is generally restricted to a few load speed applications because of _____.
what is the difference between b c d curves on mcb
how the phase convertor changes the no. of phases
difference between isolater and circuit breaker?
Why we say three phase voltage 440v.
what is the formula for hv test for cable and circuit breaker..????
why only 26v dc is used in aircraft and 115v ac in aircraft.
Why we use the D-curve MCBs in critical power distrubution.
What should be the DC voltage for Hi-pot test on 11kv switchgear
how will you find out the fuse failure by remote operation?
Isolation transformer primary to sec turns ratio?