how calculation to be done of cable size/o.h. conductor
size of 11kv h.t.for the load of 2175 kw
Answer / k.prakashchandra
The current is about 120 A. But it is not continuous.You
have to the study the list of OH conductors available in the
market.For 120 A and 50' Temp rise ,weasel ' ACSR conductor
is enough. Then you have to consider voltage regulation
which should not exceed 6% and further development. Rabbit
ACSR conductor is the next one with carrying capacity of 148
A for 30' temp rise and 183 A for 50 ' temp rise.Temp rise
is for calculation of maximum sag.
|Is This Answer Correct ?||1 Yes||0 No|
What is water cooled chiller plant?
How does "OUT OF STEP" relay ,for Synchronous motor protection, work?
For load of 1 nos 3 TR Air Conditioners,6nos of 60 Watt Tibe Lights, 2 nos 200 W Outdoor Lights,1 no Coffee maker.All may work at the same timehow do I select DG Set Rating ,pLease advise the calculations
fuses rated by amperes but not power,why?
When both contractor star & delta is hold in star delta motor ?? So what happen in this case ??
how to calculate cable size for the motor
how can we calculate the current
what ever the ups kva it may 500 kva or 500 va always out put is AC 240 volts its right?
why should we connect the no load components in a equivalent circuit of transformer in parallel?why cant it be in series.
ell me capacitor bank chossen formula.load in KW
what is the difference between induction and synchronous motor?explain in simple words?why 3 phase motor is given preference over single phase motor.
why a pilot exciter is used in combination with the main exciter? why not only a main exciter is used for excitation to an alternator?