How do you connect the capacitors on polyphase circuits?
Answers were Sorted based on User's Feedback
Answer / joseph
You can connect Single Phase capacitors to individual
phases. Alternatively you can use three phase capacitor
unit directly. Another option is to use Single phase
capacitors rated for 415 or 440V, make a delta connection,
and connect in three phase.
|Is This Answer Correct ?||31 Yes||3 No|
Answer / rai hasnain
in single phase circuit capacitor use in parallel the circuit
|Is This Answer Correct ?||14 Yes||1 No|
Answer / sheikh
Commonly in industries there are used mostly three phase load like motors. transformers e.t.c utilized 3 phase static capacitors which internally made star or delta connection
rating of capacitor denoted in KVAR LIKE 50 KVAR, 25 KVAR and others.
|Is This Answer Correct ?||10 Yes||1 No|
Answer / shyamu
|Is This Answer Correct ?||5 Yes||0 No|
Answer / abhishek
in parallel to line
|Is This Answer Correct ?||6 Yes||2 No|
Answer / h r rajyaguru
In three phase load the capacitor bank is connected for improving the power factor (P F). The rating (KVA and V) of the bank can be calculated depending on the existing system voltage and up to which P F we intend to improve. The ideal location of this Capacitor Bank is near to the load. For large size motor / load separate circuit breakers are to be used for switching the said Capacitor Bank. The motor and the bank are to be closed / opened simultaneously. Some times Capacitor Banks are connected with the Motor Control Center (MCC) or Power Control Center (PCC) for improving the P F of the system. The voltage rating shall be 10% higher than the system voltage.
|Is This Answer Correct ?||3 Yes||0 No|
Answer / venkatesha sharma
star or delta connected bank interfaced between three
|Is This Answer Correct ?||5 Yes||3 No|
In low voltage system we put capacitor bank in parallel to the PCC (POWER CONTROL CENTER) in that bank capacitors having delta connection.On HT bus series capacitor bank is used.Induction motor having long cable distance we use capacitor bank in delta connection.In large high voltage motor having large rating use capacitors bank along with reactor.
|Is This Answer Correct ?||1 Yes||0 No|
A delta-connected bank of capacitors is usually applied to voltage classes of 2400 volts or less. In a three-phase system, to supply the same reactive power, the star connection requires a capacitor with a capacitance three times higher than the delta connected capacitor.
Capacitors shall be connected near to the load.Some times Capacitor Banks are connected with the Motor Control Center (MCC) or Power Control Center (PCC) for improving the P F of the system. The voltage rating shall be 10% higher than the system voltage.
|Is This Answer Correct ?||0 Yes||0 No|
Answer / rajendran.m
Separated connections to three phase.
|Is This Answer Correct ?||3 Yes||4 No|
what is effect of length of air gap on performance of dc motor and generator?
What is the vector group of a transformer,how can it be found out?
If one lamp connects between two phases it will glow or not?
in domestic service connection,what is service main?
star delta advantage and disadvantage?
How to select KW/HP rating of motor for particular application? Is there any relationship od RPM?
what are the applications of transistors with low dc gain, high dc gain and medium dc gain( beta)?
why the starting voltage drop in a cable needs to be limited?what is percentage of the voltage drop allowed during starting?
what is the function of choke and starter in a tube light??
what is phase and neutral.
examples of resistive inductive and capacitive load
full form of electrical?