how much current capacity of 300 sq. mm cable (4 core
aluminium) and 150 sq. mm cable ( 4 core aluminium)
Answers were Sorted based on User's Feedback
Answer / vishvendra singh
we know that current capacity of Alluminium conductor is 2
AMP/sqmm. thats by In normal condition 300sqmm cable current
capacity -600 A & 150 sqmm capcity is -300 A.
|Is This Answer Correct ?||14 Yes||8 No|
Answer / k.k dash
now a days company manufacture lower gauge of aluminium cable for there own profit,previously 300 sqmm alu cable can take 600 amp,bt now a days 300 sqmm will take 300*1.2=360 amp at 80% load which is healthy for user,same way 150 sqmm will take 150*1.2=180 amp
|Is This Answer Correct ?||7 Yes||3 No|
It depends on lot of factors. The duration of the load:
short-time[as in short-circuit case],continuous load,
intermittent load. It depends on also on ambient type [air,
underground-direct laid or in concreted duct],on thermal
resistivity of the ambient [if it is in underground],on
ambient temperature, on insulation type[bare, pvc, xlpe,
epr etc.] and other factors.
Let's say in short-circuit case for 1 sec 300 square mm
aluminum conductor pvc insulated. Permissible temperature
[for PVC short-time]= 150oC.Ambient air 30oC.
Ipermissible=27 kA[27000 A].
For the same cable in open air 30oC[NEC Table 310.15(B)
(17)] continuous load [75 oC]600 MCM=300 sqr.mm permissible
|Is This Answer Correct ?||1 Yes||2 No|
Any one can explaination about calibration with rotating sub standards?
A 3ph load of 10 KW is equal to how many KW of single phase .
Transmission through a short line depends on
Differenciate between circuit wiring and sub main wiring with illustrations
What is the rating of your substation and what are the different types of substations?
what is the meaning of TPN
wht factor are considered to design ACB( air Circuit reaker) 415V
What is mean by STUB protection?
star delta connection used in reduce the starting current at 3 times . how its reduce the current please explian .
Why USe In -48 DC Volt !
at meter room 50 hrc switch installed,but there are not get earthing proper,so what happen?and 11kv transformer out put going in to hrc main 400a three nog each? so earthing is require for all switch? (some customer made earthing at there home.)
what happen when increase or decrease size of lamp,light.glass.