how much current capacity of 300 sq. mm cable (4 core
aluminium) and 150 sq. mm cable ( 4 core aluminium)
Answers were Sorted based on User's Feedback
Answer / vishvendra singh
we know that current capacity of Alluminium conductor is 2
AMP/sqmm. thats by In normal condition 300sqmm cable current
capacity -600 A & 150 sqmm capcity is -300 A.
|Is This Answer Correct ?||14 Yes||8 No|
Answer / k.k dash
now a days company manufacture lower gauge of aluminium cable for there own profit,previously 300 sqmm alu cable can take 600 amp,bt now a days 300 sqmm will take 300*1.2=360 amp at 80% load which is healthy for user,same way 150 sqmm will take 150*1.2=180 amp
|Is This Answer Correct ?||6 Yes||3 No|
It depends on lot of factors. The duration of the load:
short-time[as in short-circuit case],continuous load,
intermittent load. It depends on also on ambient type [air,
underground-direct laid or in concreted duct],on thermal
resistivity of the ambient [if it is in underground],on
ambient temperature, on insulation type[bare, pvc, xlpe,
epr etc.] and other factors.
Let's say in short-circuit case for 1 sec 300 square mm
aluminum conductor pvc insulated. Permissible temperature
[for PVC short-time]= 150oC.Ambient air 30oC.
Ipermissible=27 kA[27000 A].
For the same cable in open air 30oC[NEC Table 310.15(B)
(17)] continuous load [75 oC]600 MCM=300 sqr.mm permissible
|Is This Answer Correct ?||1 Yes||2 No|
WORKING PRINCIPLE OF HALOGEN LAMP & MEQUERY LAMP
What should be the DC voltage for Hi-pot test on 11kv switchgear
We store the d.c supply...then why can't we store A.c supply???
HI....HOW CAN BE MESARED THE VALVE OF NEUTRAL GROUND RESISTOR WHIC IS LOCATED AT SWICHGEAR ON GENERATOR SIDE....
How to select the proper VSD to operate high inertial load
The efficiency figures for energy efficient motors (in comparison with standard efficiency motor) can be generally higher by____%.
What are series and parallel isolators?
What is the de rating factor of cable? What is the importance of the de rating factor in cable selection?
Why the moulded plug comes with domestic appliances instead of assembled plug like anchor, Vinay 5/15 A.
line diagram for mcb , mccb , rccb .
watt meter have 4 terminals what there name??? and what theses 4 terminals indicates ?? and why 2 terminals are short circuited??
what is the use of terminals in transformer ?