how much current capacity of 300 sq. mm cable (4 core
aluminium) and 150 sq. mm cable ( 4 core aluminium)
Answers were Sorted based on User's Feedback
Answer / vishvendra singh
we know that current capacity of Alluminium conductor is 2
AMP/sqmm. thats by In normal condition 300sqmm cable current
capacity -600 A & 150 sqmm capcity is -300 A.
|Is This Answer Correct ?||17 Yes||11 No|
Answer / k.k dash
now a days company manufacture lower gauge of aluminium cable for there own profit,previously 300 sqmm alu cable can take 600 amp,bt now a days 300 sqmm will take 300*1.2=360 amp at 80% load which is healthy for user,same way 150 sqmm will take 150*1.2=180 amp
|Is This Answer Correct ?||8 Yes||4 No|
It depends on lot of factors. The duration of the load:
short-time[as in short-circuit case],continuous load,
intermittent load. It depends on also on ambient type [air,
underground-direct laid or in concreted duct],on thermal
resistivity of the ambient [if it is in underground],on
ambient temperature, on insulation type[bare, pvc, xlpe,
epr etc.] and other factors.
Let's say in short-circuit case for 1 sec 300 square mm
aluminum conductor pvc insulated. Permissible temperature
[for PVC short-time]= 150oC.Ambient air 30oC.
Ipermissible=27 kA[27000 A].
For the same cable in open air 30oC[NEC Table 310.15(B)
(17)] continuous load [75 oC]600 MCM=300 sqr.mm permissible
|Is This Answer Correct ?||1 Yes||2 No|
What is the importance of quality factor in resonance?
how to put cable sizing and cable glands size for respective cable & Cable Lug size in a DB sectors???
what happen if we supply ac to the field of a alternator?
Hello sir. if u have electical engineering exam paper then plz mail me at firstname.lastname@example.org. i m appearing exam for HPCL.
how we can do the insulation on secondary of ct explain and so that tan delta will within limit
I have running 4 generator in paralel.All generators Voltages is same(470 V),KW also same (100 KW) but only No2 generator Amper is high than another generators. DG No:1,3,4 470V,100KW, 150 A DG No:2 470V,100KW,400 A
why electronic instruments is more favorable than electrical?
CFL lamp is what type of load?
how the earthing point or earthing is taken for ships and airplanes?
what are the affects of loose connection in electrical circuit.
can we use ACB for HT supply
how to calculate Transformer loss?