How many straight through joint is permissible in single
core 33kv XLPE cable for a length of 985 mtr.
Answers were Sorted based on User's Feedback
Answer / sridhar
this is not compulsory to have a joint in the cable length
of 985mtr. we can plan of avoiding joint by procuring the
cable drum in single length. Advantages is you can avoid
the joint & dis advantages is handling such a heavy cable
drum due to weight & special order to be placed on cable
2. by having straight through joint in the cable, we have
to ensure that the joints are done at a proper place to
avoid any damage to the cables & to put the
identification / route marker to be placed if the cables
are going to be laid in u/g.
note:- As per the standard cable manufacturer is concern ,
the max. cable length in a drum will be 250mtrs. for this
we have to fix min 4nos. of straight through joints. By
this we are adding cost to the cables + straight through
by procuring through 1st method we can avoid the above said
|Is This Answer Correct ?||10 Yes||2 No|
Answer / ankush mitra
|Is This Answer Correct ?||11 Yes||4 No|
Answer / pankaj
|Is This Answer Correct ?||9 Yes||6 No|
We have 2 no. 4MW DG set. and GEB supply. But, we running, only 1 DG set. when we done APFC/Power factor setting : 0.90, then winding temp. Low. but when setting done : 0.83, then Winding temp. increase. WHY Why ? ? ?, plz give me answer.
we use 400/5A ct and 35/roor3KV,/0.1/root3KV,0.1/root3KV pt ratio. What is the multiple factor of this meter.
How can you calculate in detail the VA burden of current transformer used for Restricted earth fault protection? Please understand that the CT required here is Class PX or X. Also please show the calculations for knee point vtg, stabilizing resistor, magnetising current.
As you achieve greater success with the company after some years, Will you like to be a share holder in our company?
Battery is a voltage source? give one example of current source and why?
would the same effect be achieved by reversing the connection to one winding of the induction motor 3-phase?
what is phase to phase voltage? what is line to line voltage
how many joints are allowed in underground HT cable of 1 KM
how the transmission voltage ranges are decided like 11kV,33kV,66kV,132kV,220kV,400kV,725kV.... why not choose the transmission line voltage as 23kV,164kV,440kV?? what's the reason??
Why transformer neutral earthing? What is advantages?
In a HT switchboard where Nos. of Transformers are connected, how to decide Incoming cable size? Whether Cable should be rated for connected load or maximum demand?
what is the operation of UPS ? can any one answer me?