How many straight through joint is permissible in single
core 33kv XLPE cable for a length of 985 mtr.
Answers were Sorted based on User's Feedback
Answer / sridhar
this is not compulsory to have a joint in the cable length
of 985mtr. we can plan of avoiding joint by procuring the
cable drum in single length. Advantages is you can avoid
the joint & dis advantages is handling such a heavy cable
drum due to weight & special order to be placed on cable
2. by having straight through joint in the cable, we have
to ensure that the joints are done at a proper place to
avoid any damage to the cables & to put the
identification / route marker to be placed if the cables
are going to be laid in u/g.
note:- As per the standard cable manufacturer is concern ,
the max. cable length in a drum will be 250mtrs. for this
we have to fix min 4nos. of straight through joints. By
this we are adding cost to the cables + straight through
by procuring through 1st method we can avoid the above said
|Is This Answer Correct ?||10 Yes||2 No|
Answer / ankush mitra
|Is This Answer Correct ?||11 Yes||4 No|
Answer / pankaj
|Is This Answer Correct ?||9 Yes||6 No|
What is the main purpose of c.f.b.c.boiler
What are RMU yard Safety Operating Procedures
How i can calculate current of cable according to ares?
what is the purpose of silicon dropper used in battery charger?
What is neutral and how to produced
Can you any one explain different between instantaneous over current and IDMT
I have been using an 600VA with 0.6 p.f UPS with my desktop which has 450W power supply unit. Can anyone explain how can this happen . Because the output of the UPS is 360W (600*0.6) (<450W)
If we are importing real power & exporting reactive power then what will be the effect on our system
What are the components connected in between the power supply coming from an electric pole to HT & LT Panels in a large commercial building or how the power supply connected from Electric pole to Transformer & then to the HT & LT panels of a building? Please send me answers via mail, my id is firstname.lastname@example.org. If possible, please give a line diagram.
Why AC current leads voltage in capacitor and how?
why two over current realy used in vcb.
want to know about DMRC