What is the difference between automatic & semi-automatic
Answers were Sorted based on User's Feedback
Answer / v. senthilkumar - skpcl
Fully Automatic Star-Delta: In these starts Start-Delta
operation is an automatic one, which is accomplished with a
Timer fitted inside the starter. The time period from Star
to Delta can be adjusted between 7 to 15 sec. The Starter is
provided with Bimetallic Thermal Relay for protection
against Overloading & Single Phasing Conditions.
Semi-Automatic Star-Delta: These Starters are operated with
3-push button systems, in which the third push button
(Yellow) is used to change the motor running sequence from
Star to Delta. Bimetallic thermal overload Relay is fitted
in these starters for protection against overloading and
Single Phasing problems.
|Is This Answer Correct ?||26 Yes||2 No|
Answer / seimence
the difference between automatic & semi automatic starter
delta starters becouse the star delta starters are both use
in automatic & semi automatic condition so automatic
starters are work in automatic this not oparete manuali but
the semi automatic starters both are manuali & automatic
performe in ac machine.
|Is This Answer Correct ?||11 Yes||6 No|
Answer / prabhakar
Semi automatic starters will be opreated manouly which will
trip only on high voltage
fully atomatic starters will work with level
control ,timers and single phase priventers so it is fully
|Is This Answer Correct ?||8 Yes||7 No|
expansion of rccb
How does cost of generation from hydropower plant compare with other sources of electricity?
what will happen if the connections of protection ct reverse? will it burn the ct?
what is the deference between watt and KVA
how ceiling fan worked?
what is the max working temperature of an oil filled transformer say of about 1500kva.
do you know measure the earth resistance?explain
what is the purpose of vector group in a transformer ? if 2 tranaformers r connected in parallel the vector group is same or not? for parallel operation 2 transformers of different manufacturers maintain same vector group or not?
why ups rated in kva
What are the disadvantages of autotransformer?
how the testing of CT OF 400/200/100 done in33/11 kv s/s
Why electrical engineer use Cu Strip for transformer neutral why not GI Strip? What if we use GI instead of Cu does it affects the transformer performance.