The bulb of the Buchholz relay contains liquid mercury which
closes the alarm or alarm/trip contacts whenever the relay
is activated. Note that the liquid mercury closes the
alarm contacts only if the gas flow through the relay is
not serious. However, if the flow is serious both alarm and
trip contacts will close to give alarm and trip signals.
From the above explanation you can understand that liquid
mercury being a good conductor must be kept away from the
contacts under normal condition. The only way to do this is
by tilting the relay.
|Is This Answer Correct ?||10 Yes||4 No|
How can we measure earthing resistance test (Earth meggar) of Transformer neutral pit while in live condition?.
how we calculate electrical load on a building according to area?
In a star(primary) to delta(secondary) transformer,how you take the neutral point?
why resistive load has unity power factor,inductive load lagging and capacitive load leading power factor?
why test lamp didn't glow across 500v megger?
What is core CT & it's function?
what is principle of DG
what is sustainable current of any conductors . a bare busbar or pvc cable has different sustainable current .
how to select electrical equipment such as fuse,dg,transformer,motor,msb,wire,cable as per the connecting load..please mention any books to design,take licence
If a HV Underground Cable (13.8KV) is layed in the ground below 1.5 Mtrs and any building construction is done on the Cable route. IS this allowable or Not? What should be the clearance. As per ISO construction on HV cable route is safe or Not? Why? Can any body suggest the site for my question?
Dear sir, I completed DECE In the year 1995.Now i am working in a private company from last 10 years as an Electrical supervisor.The company having a 1000 KVA transformer.Now i try to apply "C" Licence. I am eligible or not.If not eligible,pls give solution.
how to select a circuit breaker?