The bulb of the Buchholz relay contains liquid mercury which
closes the alarm or alarm/trip contacts whenever the relay
is activated. Note that the liquid mercury closes the
alarm contacts only if the gas flow through the relay is
not serious. However, if the flow is serious both alarm and
trip contacts will close to give alarm and trip signals.
From the above explanation you can understand that liquid
mercury being a good conductor must be kept away from the
contacts under normal condition. The only way to do this is
by tilting the relay.
|Is This Answer Correct ?||10 Yes||4 No|
What is fault clearing time for Current Limiting Moulded Case Circuit Breaker?.
Why single core cable required bonding at double end.
How to calculate cable sizes in sq.mm. with using motor KW? Any formula there?
18 Answers Hitachi, TATA, L&T, Reliance, BRB Cable, Saha Bright Polytech, Construction, Nahar, NWPF, SGH, Techno Electric and Engineering, TFIL, Microcool Systems, Renault, Aswani Properties, Thermax,
what is the difference between delta delta and star delta connection transformer? why we use delta delta transformer since it need earthing transformer for grounding?
How to calculate VCB current rating for 2000 KVA transformer
We know flow of electron is current . But why electron flow from negative to positive and current from positive to negative?
what is diffrence between neutral and earth wire
how df/dt relay operates & how it works?
WHY ARMAD USE IN CABLE
Alternator couple to diesel engine why, Alternator couple to ac service motor with gear drive for 1500 rpm possible (yes or no) aim to low input power supply give to motor then high output power taken for alternator Please answer this question
what power factor should we maintain to get maximum benefits our organisation load is 10 MW? is it best to maintain the PF at .96 rather than Unity to save electricity bill?
What is the working mechanism of OLTC in Power Transformers????