In India,we use 230V,50HZ,where as many other countries use
110V,60HZ what r d advantages and disadvantages of each of
Answers were Sorted based on User's Feedback
Answer / shahul snfa
if we use 230v,50hz for a load say 100kw. the current for
this supply will be small when compared with 110v,60hz. but
the cable size for 110v,60hz is large due to insulation
size. an most interesting thing is only the cold countries
will use 110v,6ohz supply because the heat dissipated due
to large current will acceptable to their climatical
condition but not for india.. so the supply is depended
upon the country climatical condition and about adv &
|Is This Answer Correct ?||74 Yes||2 No|
Answer / manikiran
High Frequiencies generate High Synchronous speeds and low
voltage means that low Ironlosses....Where as the High
voltage transfer more power with same loss in the line when
compared with a Low voltage line
|Is This Answer Correct ?||26 Yes||7 No|
Answer / amr mobarak
The Problem Here With Power Consumed in Loads
If We Have A 220KW Load
We will Use Cables That Can Cary 1000 Amperes When Using 220
Volt Suppl .y
While We will Use Cables That Can Cary 2000 Amperes When
Using 110 Volt Supply .
So The Characteristic Of Each Cable Is Changed With the
on the other hand the (I^2)(R) Consumed in Cables will Be
High with 110 Volt Supply .
|Is This Answer Correct ?||24 Yes||6 No|
Answer / s c budhiraja
With 230V 50Htz supply;advantage: Smaller conductor size
for same power Disadvantage: higher danger of eletrcution
With 110V 60Htz supply,the advantage is less danger of
electic shocks but bigger size of conductor for the same
|Is This Answer Correct ?||12 Yes||4 No|
Answer / maheshwaraih
because for current saving purpose
|Is This Answer Correct ?||0 Yes||0 No|
Answer / prabakaran
The cold countries only using 110V,60HZ. Because they are need to save the machines. The cold will affect the machine parts. loss is high, so they can avoid this affects should be machine can run maximum speed. The maximum speed only increase the heat level. They want to increase the max.speed to increase the frequency that's way using 110V,60HZ. In India all climate session will present, there is no more machine fault that's way using 230V,50HZ.
|Is This Answer Correct ?||1 Yes||4 No|
Answer / raviranjan singh
as compared to other countries our Indian electronics and electrical circuits are designed on these parameters. and every country has specified by different frequencies and voltages.
|Is This Answer Correct ?||0 Yes||3 No|
Answer / shiela
High voltage supply makes the appliances run with a smaller
resistance for the same rated current. Since the resistance
is small,losses will be lesser. so India uses 230 V 50 Hz.
|Is This Answer Correct ?||1 Yes||6 No|
how much test voltage should applied for tan delta test.
Igfet is a
What is ics,icu,icw of load breaker
WHAT IS THE USE OF TERTIARY WINDING IN A STAR/DELTA TRANSFORMER ?
what is the best method of grounding in 30 MW generator?
why name plate detail HP/KW rating of a motor is different from measured value HP/KW using formula?
what is main parts of alternator.
plz send me the placement interview question and answers of whizchip(technical and apttitude)..i have an interview in next.
Why -48V dc power supply using in telecom field?
Explain What will happen when direction of field current is changed (i.e, field excitation is reversed) in the following machines? 1) Alternator 2) Synchronous Motor 3) D.C Generator ( Shunt or Seies ) 4) D.C Motor ( Shunt or Seies )
HOW TO CALCULATE THE CABLE SIZE FOR POWER CABLE, CONTROL CABLE AND INSTRUMENT CABLE
how can we decide where we have to DYn11 or other vector group transformer