Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

why we generally use 3.5 core cable or in other word 1/2
core for neutral and also confirm me that in balance
conditiob(3 phase)current in neutral will zero

Answers were Sorted based on User's Feedback

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

In a three phase circuit theoritically there will be Zero
current in Neutral. But due to un-balancing of phases
practically phase voltage becomes unequal with the result
some current flows in neutral.That is why neutral is of
half rating only.

 Is This Answer Correct ? 66 Yes 12 No

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

Neutral conductor must be 1/2 the size of other
conductor.It is theoraticaly expalin that algebric sum of
all the phases when in balannce condition then neutral
current will be zero.
Now suppose one phase fail i.e total unbalace condition its
neutral conductor will provide a return path and its
current will be half the load on other phases.so by this
result on neutral conductor for every unbalance condition
its current will not exceed the rated than other phases.

Pardeep.kumar
Engineering Dept.
Panacea Biotec Ltd.

 Is This Answer Correct ? 24 Yes 8 No

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

Normally Neutral conductor is 1/2 the size of other
conductor.It is theoraticaly expalin that In a three phase
circuit ( Equal load in all three phasse) there will be
Zero current in Neutral, Ex. 3phase indusction load (Motor)
(NO NEUTRAL CONNECTED T OANY MOTORS AS THE RESISTANCE OF
THE THREE WINDINGS ARE EQAL).
But in a three phase to single phase distribution
(Resistive loads) it is not possible to maintain the equal
load in all three phases hence the unbalance current has to
be taken away from the circuit for the healthy opertion of
the equipmetns.
Thearitically and also practically it is prooved that the
flow of unbalance current in the 3 phase resistive load
distribution is always less than 1/2 of the phase current.
So 1/2 caore has been taken as a neutral

 Is This Answer Correct ? 10 Yes 5 No

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

The choice of whether to use a neutral of equal size to the
equipment. The difference of the load being delta, floating
star or star with a neutral point

A 3 phase circuit in balance will produce little or no
neutral current contribution.

However a 3 phase circuit imbalance will produce neutral
currents as per the following formula
A^2 + B^2 + C^2 - AB - AC - BC).

A three phase circuit wired in star with the neutral at the
star point will operate with null balance if the loads are
equal, it is possible (and I have seen this) for 2 phases
to fail and leave one phase connected to the load and
neutral. The neutral current becomes equal to the phase
current, the designer of the circuit failed to account for
this, the undersized 1/2 neutral overheated and caught fire
destroying the switchgear and damaging the furnace.

I would urge anybody to carfully consider all possible
outcomes when choosing neutral cable sizes as flames coming
out of a switchboard often alarms the unwary.

 Is This Answer Correct ? 2 Yes 2 No

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

Generally it depend on load, If cable is used for inductive
load e.g.motor, if there is any fault then 1/2 core is
sufficient to carry fault current due to lagging power
factor. However, in resistive load we are using 4 core
cable since there is no power factor.

 Is This Answer Correct ? 9 Yes 21 No

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

for using 3-phase supply in any instrument neutral is also
required since neutral capacity is just half to the phases.
we dont need to use 4 core thats cost matter..

 Is This Answer Correct ? 0 Yes 24 No

why we generally use 3.5 core cable or in other word 1/2 core for neutral and also confirm me that..

Any switch mode power supply (computer, UPS, AC/DC
transformer) has some leakage current and imbalance. In
data centres they are starting to use full size neutral
cables to account for this. Basically only need 1/2 size in
motors, saves money on expensive copper

 Is This Answer Correct ? 5 Yes 36 No

More Electrical Engineering Interview Questions

SUTIABLE FOR ohm's law super conductor

avr is an automayic voltage regulator ... it regulates voltage before it synchronise with grid after synchronisation it regulates power factor why....

how to calculate a cable size while load is given in amp or kw and length is also define.?

What is static Device & Mechanical device? Is transformer a static device?

4.In which type of welding is a pool of molten metal used.....

what is the path of thunderlightening? once both a buffalo and a person were standing 5m apart but lightening hit and killed buffalo not person?

why we create vaccume in transformer tank before oil filteration?

What cmos is and its benefits?

how we control the magnitude of a generator output

why rating of motor in HP?

we all know voltage is a force(emf), and the force always devides if 2 or more than2 loads are there but why does the voltage remains same is parallel, it must devide na ???

BSNL TTA EXAM QUESTION

Categories
• Civil Engineering (5081)
• Mechanical Engineering (4448)
• Electrical Engineering (16620)
• Electronics Communications (3915)
• Chemical Engineering (1093)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2994)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (171)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1378)