Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

why in three phase 440 circuit in all phase current is
almost equal L1-35 A,L2-34 A ,L3-31 A but in nutral when i
check with clamp meter it shows 25 A?

Answers were Sorted based on User's Feedback

why in three phase 440 circuit in all phase current is almost equal L1-35 A,L2-34 A ,L3-31 A but i..

Principle is vector summation.
Ir + Iy + Ib = 0

and not arithmatic summation.

Since neutral current is substantial 25A, the three RYB
vectors are not 120 degree apart. Means powewr factor in
each phase differs drastically. Thats why though there is
no much difference in RYB current, neutral has substantial
current.

 Is This Answer Correct ? 15 Yes 1 No

why in three phase 440 circuit in all phase current is almost equal L1-35 A,L2-34 A ,L3-31 A but i..

In balance condition neutral current is zero. Flux in all
three phases are in addative nature.
flux in R + flux in Y + flux in B = 0(zero)
but in your case it is different because of differnt
currnet in phases, which will affect and cause a unbalance
condition, will produce a flux in neutral and current
flowing through neutral. But in your case it is 25A which
is to much unbalance condition.

 Is This Answer Correct ? 4 Yes 3 No

why in three phase 440 circuit in all phase current is almost equal L1-35 A,L2-34 A ,L3-31 A but i..

1)your point of measuring to conder again

2)check whether nutral joint is given to another load which
you not considering for this load

 Is This Answer Correct ? 0 Yes 0 No

why in three phase 440 circuit in all phase current is almost equal L1-35 A,L2-34 A ,L3-31 A but i..

valve of currents and voltages depend upon the manner in
which the 3 phase system connected,either in star
connection or in delta connection

 Is This Answer Correct ? 1 Yes 4 No

More Electrical Engineering Interview Questions

what is mean by induction & conduction principle ? how they differ from each other ? thank you

How good are you in resolving the commercial issues to Employer's advantage?

how the testing of protection CT Testing done through Primary injection kit please describe in detail procedure...

Define norton equivalent circuit?

Is it required to do earthing in 2nd shop if earthed armoured cable is laid from 1st shop ?

11Kv Dog conductor 6/0.186 formula Line Losses ? Length 4.85Km amper ..? 52 Pole Max Load 3200Kw

if the transformer at full load have a iron loss =900w and copper loss = 1600w . what percent of the load will the transformer has a maximum efficiency?

how to calculate singlephase motor efficiency?

Explain the different regions in frequency response?

Everybody Knows What is ACB, VCB but anybody tell me what is ST?

Why battery rooms painted with dark colour

What is the exact load current needed for a place which has 100nos of bulb of each 100w?

Categories
• Civil Engineering (5074)
• Mechanical Engineering (4445)
• Electrical Engineering (16594)
• Electronics Communications (3915)
• Chemical Engineering (1092)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2986)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (122)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1377)