Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

how can we know cable size for a given current?
if any one have catalogue plz mail to
vijay_raju369@yahoo.co.in

Answers were Sorted based on User's Feedback

how can we know cable size for a given current? if any one have catalogue plz mail to vijay_raju3..

The selection of a cable size for a given value of current
can be done using the cables & tables provided by the cable
manufacturer. The selection of cable size also depends upon
the lenght of cable from source to load. The total voltage
drop should not exceed 2.5% of rated voltage. Following
factors shall be considered while selecting a cable for

1. Rated Current.
2. Capacity of Protective Circuit Breaker used.
3. Total Length of cable.
4. Total voltage drop.
5. Laying Method.i.e. underground,in conduit,in trays etc.
6 No. of cables.i.e. grouping factor.
7. Ambient Temperature of installed area.
Temperature Correction Factor to be applied.
8. Type of cable. i.e. singel core,multicore,PVC insulated,
Armoured, XLPE insulated etc.

 Is This Answer Correct ? 25 Yes 2 No

how can we know cable size for a given current? if any one have catalogue plz mail to vijay_raju3..

For an aluminium conductor we can load approximately 2.5
amperes and for a copper conductor aroundf 6 amps

 Is This Answer Correct ? 20 Yes 7 No

how can we know cable size for a given current? if any one have catalogue plz mail to vijay_raju3..

Two things are very much common on the power system engineering field while doing a cable sizing, these are:
1)LT
2)HT

Cables are separately sized based on voltage levels as said above.

Formulas used for LT side:

Full load current = KW/(KV x sqrt3 x PF x &#951;)

Voltage Drop =
sqrt 3*IFL*(R COS Ø + X SIN Ø)*L/(KV*10000*N.R.)

where

KW = Rating of the Load connected
KV = System Voltage
R = Resistance of the cable in Ohm/Ph/KM
X = Reactance of the cable in Ohm/Ph/KM
L = Length of the cable in meters
N.R = No of Runs of the cable
cosØ = Power factor of the system
PF = Power factor
&#951; =efficiency

Voltage Drop =
sqrt 3*Ist*(R COS Ø + X SIN Ø)*L/(KV*10000*N.R.)

where Ist=starting current which can be 6 times the FLA of current.In technical term it is called as LRC(locked rotor current)

HT side:

Full load current = KVA / KV x sqrt 3

Short circuit current :
A = Ish x sqrt(t)/ k

Where
t = short circuit time in sec
k = constant
A = Conductor size in Sqmm
Ish = Short circuit current in Amps
Derating Factor :

Ambient temperature correction factor for cables laid in 0.9 Trays at 50 degree C = 0.9

Group derating factor:

Multi Core cables
Cables are laid with a spacing of one Diameter and routed in cable trays and trays in tiers by 300mm =0.9
Ageing factor= 0.95
Therefore the Total derating factor = 0.9 x 0.9 x 0.95 = 0.7695
Total Derating Factor= 0.77

The rest calculation for voltage drop are same as that of LT side

 Is This Answer Correct ? 8 Yes 3 No

how can we know cable size for a given current? if any one have catalogue plz mail to vijay_raju3..

roughly you can take it as 1.5 times of the conductor
size.eg. 300 sqmm can conduct 450 A approximately and
moreover it also depends on the application like

if you want in detail you can check it in finolex website.

 Is This Answer Correct ? 12 Yes 9 No

how can we know cable size for a given current? if any one have catalogue plz mail to vijay_raju3..

Thank U very much VASU

 Is This Answer Correct ? 6 Yes 3 No

More Electrical Engineering Interview Questions

if we give DC suply to the AC motor what hapen

Why we apply only reduced voltage to the alternator while conducting slip test ? also the current increases to a larger value with reduced voltage itself Why ?

Hai, I am from EEE branch.On feb 17 iam going to write an Exam for hindustan petrolium corporation Ltd.So plz send me the written exam pattern/Q's/interview questions.please mail to yuva_polisetti@yahoo.co.in

What is the significance of %Z in case of transformer?

1) name the communication cable and how it is communicate in between plc to modbus , plc with hmi? 2)name of the communication cables?

how the synchronizing is obtained at bus couplers in grid substation? (because there we cannot change the frequency in one of transmission lines like in generator synchronization)

if 300 hrs not comleted at wat interval b.c,d checks og take place

explain working of differential protection for a transformer?

WHAT IS A COLOUR CODING OF 3 CORE CABLE

Hydro P.P. run @ 600 rpm,8pole, Nucler P.P @ 1500rpm 4 pole , ThermlP.P @ 3000 rpm 2 pole.Why this diffrence??? when we can generate electricity @ 600 rpm then Why we had incresed speed in NPP & TPP???

How to calculate the average power factor in 3 phase unbalanced system

why the power cut problems occur in tamil nadu? may i know the exact reason.plz

Categories
• Civil Engineering (5074)
• Mechanical Engineering (4444)
• Electrical Engineering (16594)
• Electronics Communications (3915)
• Chemical Engineering (1092)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2987)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (122)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1377)