How to calculate load requirement of a 50 flat apartment with 5 kw each unit,sizing of cable,transformer

How to calculate load requirement of a 50 flat apartment with 5 kw each unit,sizing of cable,tr..

Each unit as in each flat 5kw ?? That would be 250kw for 50 flats.
250kw into 1.8 would be total current = 450amps
Cable sizing Acc to Dubai STDs for 450amps would be
2runs x 4C 150sq.mm Cu + 1C 150sq.mm ECC

Transformer sizing u need to take into account 20-25% future use efficiency of t/f and diversity factor

So for 250kw it would be 250x1.2x.8/.9 nearly 300kva transformer.

 Is This Answer Correct ? 4 Yes 0 No

More Electrical Engineering Interview Questions

whytransformers rating in KVA?

While performing stability test of differintial cts how to know the voltage and current on both side of the transformer?

what is the magnitude of earthing and neutral voltage

what is the difference between MCCB and SFU in terms of their application?

How can you measure battery AH?

Define average demand?

how to connect the three phase capacitor in three phase star/delta connection motor?

Explain what is electric traction?

What is the formula for calculating the Instantaneous Short Circuit & overcurrent for any breaker

What is Harmonics & what are its efect & which harmonic is dangerous

what is skin effect? why is it absentin dc system

why we are using the ac supply in domestic purpose why don't use dc supply

Categories
• Civil Engineering (5085)
• Mechanical Engineering (4451)
• Electrical Engineering (16632)
• Electronics Communications (3918)
• Chemical Engineering (1095)
• Aeronautical Engineering (239)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (259)
• Instrumentation (3014)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (124)
• Power Plant Engineering (172)
• Textile Engineering (575)
• Production Engineering (25)
• Satellite Systems Engineering (106)
• Engineering AllOther (1379)