How to adjust the zero & span of a control valve from the
Answer / ashish b. patel
when you are open the positioner there are two setting, zero & span. positioner to give 4 mA and set the Zero adjust and valve should be 0% open. after give 20 mA and set to span and valve should be 100% open. this to adjust are very important. after you can give again 4 mA- 0%, 8 mA- 25%, 12 mA- 50%, 16 mA- 75%, 20 mA-100%.
|Is This Answer Correct ?||8 Yes||0 No|
What is seismic transducer?Where it is used?
why using 4-20ma not using 0-20or why not using 1- 20ma???????
what is o2 analyzer and how it measured ,what is the role of this analyzer in cfbc boiler...
what are the steps to commissioning a DCS system?
why orfice is not used for main steam flow calculation
why we use 4-20 mA to do calibration of the instruments.why we cant use 0-20 mA?
when we are using HART COMMUNICATOR why we are using 250 ohm resistance while using HART COMMUNICATOR.
wht is loops ? how many loops are there?
What is the difference between instrument earthing and normal earthing? and why is it necessary to do so?
can any one help me to get bel probational engineers sample question papers. I have applied for it.
Hi my friends Is any one who can assist me in knowing the typical interview questions for system engineer at General Electric pty Ltd
what do u mean by 2/3 soleniod valves?