A group of machines (wind turbines) connected with 33KV
feeder and each machines are having individual VCB. The 33KV
feeder connected with 110KV/33KV substation. The 33KV feeder
tripped by over current at Substation and fault recorded at
Substation as OC-R&Y phase. Same time the group of machines
VCB tripped by over voltage, the fault recorded voltage was
above 66KV by numerical Under/Over voltage relay. While grid
drop time, this much of voltage hike is possible?
The load throw-off may result in run-away speed being equal
to twice the normal speed ,hence the voltage may also become
twice. Over voltage relay should be set at not more than
120%.You can employ the AVR so that the voltage does not
increase with the speed.
|Is This Answer Correct ?||1 Yes||0 No|
how to calculate bus-bar sizes? (copper bus-bars)
What is the difference between MPCB and OLR?
what is 30-phase of transformer
Why are transmission lines multiples of 11? Is it because of some historic reason ? Or is there a scientific base to it?
what is role of mpu in dg
What is the purpose of stand by earth fault protection for transformer ?
why are the likely reasons for bochholz & pressure relays oprate due to a internal fault but not differential relay ?
1 HP = how many Kva
How to calibrate or test an LT Air Circuit breaker 440 volts, 35 KA, 800 Amps ?
In constant power region of 3-phase IM torque-speed characteristics, if frequency increases slip A does not alter B decreases C increases D none of above
what is hourly consumption of coal in therma plant
what is meant by dielectric breakdown ? where we using HV test kit & what purpose?