If a control valve is hunting means means if we are giving
50% to the cv, the cv will open at 51% then slowly slwoly
it will reaches 49% , then it will reaches again 50%, this
type of action occured frequntly.. so what to do for solve
this problem. The possible cause is in volume booster or
positioner's relay.. positioner is double acting .. and
make siemens..sipart.The cv is double acting and mounted
for anti surge operation, it having 4 nos. volume booster,
one sov, one positioner, etc..?
Answers were Sorted based on User's Feedback
Check the following items:
1. Any loose connection or leakage of pneumatic signal.
Check all tube fittings with soap solution.
2.Check the gland packing should not be so tight. If feel
tight, get loose them a bit.
3. Check the pneumatic relays of Postioner. Get clean its
ports, nozzle, flapper etc.
4. Also check, that linkage, feed back mechanical link
should not have any dent, grove, burs etc.
|Is This Answer Correct ?||17 Yes||0 No|
Answer / avinash d. pagar
Also please check volume booster function separately with
out positioner and then set factory setting of positioner.
again calibrate positioner by auto calibration. mostly
hunting and over shooting issues cause by booster error.
|Is This Answer Correct ?||3 Yes||0 No|
Give 2 application of quartz crystal used for process parameter measurement.
Dead weight tester & comparator for calibration , which is more accurate , what is the application.
why is honed type flow orifice plate? what purpose it used? how to select this?
What are the error values can accepted in flow transmitter calibration?could u give any formula for this?
what the differant between Wet Leg /Dry Leg
what is cascade loop and how it work and why it used instead of PID single loop? In cascade, Which loop is faster and slower? Please explain with loop drawing and example...
What are the two states of a controller
What is the procedure of calibration of Load cell?
In split range control, we will control 2 outputs with time interval. Eg :(with 4-20 ma signal, for 4-12 ma we are operating one control instrument like valve & for 12-20ma we are operating other control instrumet (other valve). If we get a signal of 15ma to first instrument (Valve 1), what will happened to the first valve, and if we get signal above 20 ma to 2 valve what will happened ?
Sir i am preparing for PSU exam for ONGC but i am not able to get the appropriate syllabus and previous year question papers. Kindly send me the same, that will be a great help from ur side. OR if anyone can plz send me the papers and syllabus please.
what is meant by nuclear collector?
any one can send me instrumentation previous interview papers? I prepare for MNC Company Interviews? my mail id- Rakesh.Golla@dodsaldxb.ae , and another mail email@example.com