1. Synchronization is not required
A. Thermal B.Hydel
Answers were Sorted based on User's Feedback
Answer / sajid
|Is This Answer Correct ?||15 Yes||2 No|
Answer / lava gaur
|Is This Answer Correct ?||0 Yes||6 No|
Befor synchronissation of Generator what test to be carried out.pl.specify with reason.
some basic standard questions on transformer.
What is the difference between Class PX & Class X CT's
What will be MF if we have CT ratio is 130 of 3 nos?
I want to ask a question which i faced during testing of Capacitive Voltage Transformer in AIS. We have measured the C1 , C2 individually , but when we start to measure the total C1+C2 , the testing equipment shuts down and says low loading. Kindly is it possible to find the total capacitance by using measuring device. kindly briefly explain the procedure.
WHAT HAPPEN WHEN CT SECONDARY OPEN DURING LOAD
is there or does RCCB work for single phase connection?
What is diversity factor in electric installations?
What is pole of the system?
What is the importance of earthing?
what is surge impedance loading?
How to do the REF Stability test for power transformers in Site?