Why 24VDC power Supply is used as standard for all loop
Answers were Sorted based on User's Feedback
Answer / lokendra
as per ISA standards 24 VDC is the minimum possible voltage
at which the spark will not come,we know our transmitters
will give max output current of 27 mA here they have limit
this current bcause the power we get is less than 1 watt
(P=VxI)648mW which is not capable of producing a spark thus
they have avoided spark generation by selecting 24 VDC and
limiting currnt to 27mA.this comes under extrisic safety.
|Is This Answer Correct ?||47 Yes||6 No|
Answer / sivakumar
see all loop powered transmitters are capable of
withstanding 10 t0 36v dc ...as per the process requirement
it will vary.. insome industries they are using 12v dc
also.. 24 vdc is used because as per ISA there are some
standards wich will match other process reqirement like
24vdc relays for digital control also wecan use 24dc to
energize tis relays
|Is This Answer Correct ?||10 Yes||6 No|
Answer / sagar
Because 24vdc is a minimum voltage where no possibilities of any kind of spark.
so we can prevent our costly instuments using 24 vdc.
|Is This Answer Correct ?||6 Yes||2 No|
Answer / venkatesh
all transmitters(24vdc) are using for very imp parmeters , so the 24v dc coming from smps or any dc power units and these working with 230v ac UPS SUPPLY so if anytime some powertrips will come this transmitters still working with on ups supply with smps outputs
|Is This Answer Correct ?||0 Yes||0 No|
Answer / maddy2504
It totally depends, 24 V DC 2 wire is not always applicable
every wehere some times it is 2 wire, 3 wire (2 cable for
power up & signal & 1 cable is for earthing), some times it
will 4 wire(2 for powerup & 2 for signal).
24 V Dc is for certain limit b'coz voltage will be drop in
that case w'll use 230v AC.
|Is This Answer Correct ?||5 Yes||6 No|
Answer / abdul
Give extra power supply damage this device because standard instrument give standard electrical signal 4-20 and 24 V dc
|Is This Answer Correct ?||0 Yes||1 No|
Answer / ankur gupta
it is not possible to design capacitors,resistors with
greater ratings.since size is the restriction.
|Is This Answer Correct ?||6 Yes||15 No|
while i check zero check for dp flow transmitter some fluctuating came (0 to 458 kg/h) what is the reason?
how to change measuring units from mmwc to cubm/h in rosemount air flow transmitter with hart communicator fluke 744
what is dry leg and what is wet leg?
WHAT IS THE DIFFERENCE BETWEEN A TRANSMITTER & A SMART TRANSMITTER.
What is Cryogenic?
Someone Please tell me what are the Pre-Commissioning activities in a Thermal Power Plant for an instrumentaion Engg.
testing of thermo-couple?
what is the formulae to find the thermocouple output to temperature
admittance level sensor meaning?
why r using 250 resistances
Why we use the remote seal transmitters
IS there any effect of vortex in low pressure side of the transmiter after the orific in feed water line? if yes then what is the calculation?