why nearly all the voltage levels are in the multiples of 11
like 3.3 ,6.6 ,33 ,11 kv.....
Answers were Sorted based on User's Feedback
Answer / nisarg d. patel
In India we provide an offset of 10% overload on the rated voltage level to easily accomodate the varying overload.So in accordance with this, 10 KV becomes 11, 60 KV as 66 and so on and so forth.But this convention is not followed in EHV above 500 KV where we follow the international transmission voltage levels like 730 KV, 1200 KV and so on.And also because the form factor is 1.11 so it becomes symmetric to have the transmission level as 1.1, 3.3 etc.
|Is This Answer Correct ?||5 Yes||0 No|
Answer / kolhe g j
Transformer changes the voltage level. Form factor for
sinusoidal AC 1.1 .
|Is This Answer Correct ?||9 Yes||5 No|
Answer / brijesh
Because of form factor that is 1.1
|Is This Answer Correct ?||4 Yes||2 No|
Answer / ashi
its due to form factor
|Is This Answer Correct ?||3 Yes||2 No|
Answer / e.subash chandrasekar
Because of form factor 1.1
|Is This Answer Correct ?||1 Yes||1 No|
Answer / k.sahadevan nair
In India and other commonwealth countries, in the initial stage maximum generation voltage was 11 KV considering maximum available insulation rating. In order to step up this voltage,secondary of transformers should be 33 KV, 66 KV, 110 KV ,132 KV, 220 KV etc. So HT voltage of all step up/down transformers were fixed at multiples of 11. This has become a practice. This has nothing to do with form factor 1.11
When generation voltage is improved due to advancement of technology it has become difficult to change rating of all existing transformers. Naturally rating of transmission voltage of multiples of 11 continued and still going on. This is not applicable to EHT as this is a recent development and limited to certain countries only.
|Is This Answer Correct ?||0 Yes||0 No|
Answer / er. akil
at 11 kv level losses should be minimum
|Is This Answer Correct ?||0 Yes||7 No|
what is function of reactor coil in Power factor correction panel
what happen "when Dyn11 is parallel operation with Dyn1"?
1.dg on load alarm/stop alarm... 2.dg on load. piu alarm alarm kaise chek krte hai
how make megger test for control cable like 12c x 1.5mm and what it apply voltage and test timing details.
What happens if we give the supply to the rotor of induction motor and make its terminal shorted?
the problem faced on star or delta winding connection??
If any HVDC line is going with positive & negative(the negative usually have return path of current with earthing electrode). Now the question is if this HVDC earthed electrode which is using as return path and earthed any nearby 400kv or 220kv AC substation equipments. which will be the impact of this on AC substation & its equipment, how severe may be this and what should be the minimum distance require between HVDC earthed electrode and AC substation equipments? It's really an high engineering level question...Dare to answer and increase your knowledge.
How can you calculate in detail the VA burden of current transformer used for Restricted earth fault protection? Please understand that the CT required here is Class PX or X. Also please show the calculations for knee point vtg, stabilizing resistor, magnetising current.
Transformer how to maintaince a check b check c check d check
I need a formula to calculate the size of cable as per load but in the terms of length. Please Reply me as i search lot of sites but i did not get the answer.
Do you know what is dry-out test in x'mer
without name plate detail of blower how we can find out the HP & Rpm ? the input voltage is 230v single phase