If DG runing time neutral is disconnected what will be the
effect in Engine and Electricial panel.
Answers were Sorted based on User's Feedback
Answer / bndas
In case of Eart Fault during duration of without neutral
E/F relay will not work. Thus, prolong E/F insulation will
damage insulation, which will eventually land into bigger
This is a brief ans at this moment, since I don't have time
to write in more detail.
|Is This Answer Correct ?||0 Yes||0 No|
Answer / pillay
if the DG is not loaded nothing will happen and there wil be
no damage.While loaded if the load has got no single phase
load also nothing will happen and everything will continue
as normal.If you have connected a load of single phase
nature and if the load is balanced or near balanced then
also if the neutral is removed no damage will happen or you
may not see any changes because the neutral current is
balanced at the phases. but if you have connected an
unbalanced load or the load changes often than the voltages across the phases will be inconsistent.this is a very
damaging situation because the voltage can be as though you
have connected across a 2 phase supply the voltage across
the circuit is determined by the amount of current flow in
|Is This Answer Correct ?||2 Yes||3 No|
why selected genration, transmission or any at 11kv, 132, 220, 220 or 440 voltage which is propotional to 11. why does not any for ex. 12 kv 13kv or any
Pl. brief about break-down maintenance of machine tool.
what is meant by star/delta voltages as 440/220 in a 3 phase induction motor, and why it should be connected on STAR IN 3 PHASE SUPPLY
Whay you want to change your job.
How to calculate phase to phase difference ?
How to Convert horsepower to kva? what is the three phase formula? explain me if u can Example..i have 50Hp Moter how can i convert in kva tell me formula three phases Rehan Smileavail@msn.com
how to find the Motor,s insulation Power?
what is the role of reactive powerin transmission and distribution?
What is the work of IGBT in ups?
what is distribution board and panel board
technically, what is the reason behind starting the motor star the delta connection .. and what other ways to do this rather than using " star-delta transformer"
what is the difference between squirrel cage & slip ring induction motor?