my temperature transmitter in field showing 700 degree , whereas in dcs showing 459 degree, how to resolve this?
Answers were Sorted based on User's Feedback
1) Most likely, the 4-20mA scaling (what the 4-20mA represents) is not the same on the transmitter as it is on the DCS.
The scaling has to match, that is, be the same on both the transmitter and the DCS analog input.
2) A ground loop will cause an offset. The offset can be negative or positive, depending on the polarity of the ground loop.
Eliminating ground loops can be a major task, so most times, a loop isolator is used to isolate the transmitter from the DCS, which eliminates the ground loop.
|Is This Answer Correct ?||5 Yes||0 No|
Answer / shahid
Carl Ellis is give the good answer that is the technical error that may occur but some time there is possibility of miss matching in the range of DCS & the field transmitter.That's why should check the both ranges of URV-LRV.
|Is This Answer Correct ?||2 Yes||0 No|
Answer / maheshrp
Reason of DCS and field equipment range different so dcs and field variable reading
So dcs & field range same as problem your solve
|Is This Answer Correct ?||2 Yes||2 No|
Answer / raghubir nishad
Range Can match in Field instrument or PLC/DCS both side.
|Is This Answer Correct ?||0 Yes||0 No|
Why do we use triad cable for RTD to Temp.transmitter connection? Why we don't use 3 core cable?
Sir , i have completed my M.Sc In Instrumentation and presently working in Maintenance department 3 yrs Exp , is there is any possible for work in offshore ..
please send the sample qustion paper for iocl written test ..
what is vfd(variable frequency drive)?type of vfd.
what is positive feedback and negative feedback?
how to calibrate load cell
what is cavitation ?
Can someone give a detailed chart on the temperature ranges which can be measured by various temperature sensors.
In RS 500 SLC 5/03 input change one module card to another card, plz. give steps clearly.
What is difference between reset and initialization in system.
Dear Sir/Madam,im going to attend Hpcl written exams on feb 17th in instrumentation stream..can anyone send me the HPCL model papers and pattern of HPCL ....i ve not yet attended anything in HPCL...so i dont know how it comes...so just i need some model test papers and pattern ..pls help me friends...
Instrument QA/Qc what is the project quality plan?conduit inspection RFI. which documents attache with package?