my temperature transmitter in field showing 700 degree , whereas in dcs showing 459 degree, how to resolve this?
Answers were Sorted based on User's Feedback
1) Most likely, the 4-20mA scaling (what the 4-20mA represents) is not the same on the transmitter as it is on the DCS.
The scaling has to match, that is, be the same on both the transmitter and the DCS analog input.
2) A ground loop will cause an offset. The offset can be negative or positive, depending on the polarity of the ground loop.
Eliminating ground loops can be a major task, so most times, a loop isolator is used to isolate the transmitter from the DCS, which eliminates the ground loop.
|Is This Answer Correct ?||5 Yes||0 No|
Answer / shahid
Carl Ellis is give the good answer that is the technical error that may occur but some time there is possibility of miss matching in the range of DCS & the field transmitter.That's why should check the both ranges of URV-LRV.
|Is This Answer Correct ?||2 Yes||0 No|
Answer / maheshrp
Reason of DCS and field equipment range different so dcs and field variable reading
So dcs & field range same as problem your solve
|Is This Answer Correct ?||2 Yes||2 No|
Answer / raghubir nishad
Range Can match in Field instrument or PLC/DCS both side.
|Is This Answer Correct ?||0 Yes||0 No|
Where should we terminate the shield and why?
Can I put my meter across an RTD to check it safely witout tripping the equipment when it is connected to an monitoring device eg.RTD module or IQ 1000
What is expansion of SMART Instruments? And What is it?
please send me the inteview questions in IOCL
please any body have most important data for study for saudi aramco test of instrument QC thanks email email@example.com
what diffrence b/w plc s7200,300,400
why use 50% lel methane gas concentration for gas detector calibration instead of 60% lel gas concentration whereas the hi alarm set at 60% lel.
what is SIL 1 2 3
what is the calibration procedure for magnetic flow meter @ onsite
if we open the inlet of an air regulator ,how it will affect the out put of regulator? (out put of regulator is using to operate an on-off valve.it is an air to open valve,and valve is in open position.my doubt is air regulator will hold the valve in open or not,if there is no consumption or leak in regulator out put side ,we only loose the input pressure.)
how to calculate range of Dp transmitter
is here anybody who knows how to calibrate the pressure transmitter? ONLINE