there is a # KVA Transformer of 11 KV/440V, in simple(not use formuia) how can you calculate it's HT & LT side current.
Answers were Sorted based on User's Feedback
Answer / guest
Dear P.Kalivada 100KVA transformers total power (3 phase) is 100KUA one phase give 33KVA, Phase voltag is 11/1.732 = 6351 volt therefore current is 33000/6351=5.1 amp (at unit pf). You can see a name plate of 100KUA 11KV/433v tranrsformer it is written 5 amp as HT Current and 133 amp as LT side current you can verify any tranformer whose primary voltage is 11KV it's current is approximately to #/20 and secondary side of 433V it's current is approxhmately to # +#/3 ( # is how much KVA)
|Is This Answer Correct ?||15 Yes||4 No|
Answer / sunit
this is simple .. assume a 100kva tr, ok
then p= vi ( power = voltage x current)
1.lets see for HT side
p( kva)= root 3 ( for 3 phase)x voltagex current
=> kva = root3xvxI
=> I= 5.25amp/phase
2. similarly in secondary side means LT side
=> I= 144amp/phase
|Is This Answer Correct ?||8 Yes||4 No|
Answer / guest
HT side current = #/20 LT side current =#+#/3 ie 100KVA 11KV/440V transformer it's HT side current = 100/20=5 amps LT side current=100+100/3=133 amps. this is approximatelly figure(answer), Line man of Power Distribution Company fallow this method .
|Is This Answer Correct ?||7 Yes||6 No|
Answer / zaman
5KW capacity motor stare connection 410 volt pf 1 current 7.5 amp how mouch current carry of delta connection
|Is This Answer Correct ?||0 Yes||0 No|
Answer / prashant kalivada
KVA = KV x A
= voltage in KV x current in ampere
So, A = KVA / KV at HT side
therefore if KVA is 100 and KV is 11 then
A= 100 / 11
= 9.09 Amps at HT side
and for LT
A = KVA / (V/1000)
= 100 / (440/1000)
= 100 / 0.440
= 227.27 for LT side
|Is This Answer Correct ?||6 Yes||10 No|
What are the relays in ACB and VCB
1.4 What is meant by CT knee point voltage and how would you determine it
Re: how to calculate diesel consumption of a D.G.Set? Answer # 1 We can not calculate the diesel comsumption...depending upon load it will conume the diesel...suppose the 1500kva D.G is running and the load is 1000kw means it will consume 150-200 liters per hour....
66kv under ground cable how to layaing in ground any special case two ckt r runing
What is DC series motor?
what is the relation between the size of the machine and the frequency? (when the frequency increases the size of machine will increase,why?)
Why restricted earth fault protection is needed? Why can’t differential Protection is sufficient?
why phase always came one direction in 5pin socket(right hand or left hand) which direction and why..........?
What are the transformer losses?
How many kinds of E.L.C.B and how to work E.L.C.B
How to determine earth fault level to set relay for a normal distribution system of 11 kV , 100 A load????????
how to convert single phase supply to 3 phase or 3 phase to single..?