Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

In a 3Ph induction motor(old) 6 wires came out from terminal
& not mentioned u1,v1,w1,u2,v2 & w2. how can find out the
terminals? how can connect to star delta starter??

In a 3Ph induction motor(old) 6 wires came out from terminal & not mentioned u1,v1,w1,u2,v2 &a..

first of all you have to use multimeter to identify the
coil teminals. segregate it in two lines as 2 x 3 . ie top
3 terminals and bottom 3 terminals.

Next take a Small DC power supply with 3 volt and a
milliampere meter( DC ). connect this voltage to one of the
coils with milliampere meter in series( Milliampere meter
should be of center zero type ) close the supply voltage to
the coil with make and break it immediately. observe the
deflection whether it is on forward side or reverse side.
and mark one terminal for whcih +ve suplly is connected as
Start and the other ( _ ve )end as Finish. do this
process for other two coils also. once you know the top 3
start points and finish points of the coil. you are almost
there. now you short ckt all finish ends. you are left
with 3 start terminals. ie your STAR connection.

For Delta connection connect finish end of the first coil
to start end of the second coil, finish end of second coil
to start end of third coil and finish end of 3third coil
to start end of first coil. now you have theree junctions.
now your connection is in Delta mode.

 Is This Answer Correct ? 17 Yes 2 No

More Electrical Engineering Interview Questions

6. A DC AMMETER HAS R=0.1 OHM & CURRENT RANGE IS 0-100 A IF THE RANGE IS TO BE EXTENDED TO 0-500 A THEN METER REQUIRES SHUNT RESISTANCE OF ..........

In a power system we know that if the generated power is less than the load then the frequency of the system is decreases.So does this mean that total required load is delivered at alower frequency?

How works the AVR in DG Sets Plz explain??????????

Why overhead transmission line in triangular shape?

What is Specific Gravity of the Electrolyte used in Lead Acid Battery????What is Unit????

What is meant by single line diagram?

in dc shunt motor if field winding is shorted then

A 3ph load of 10 KW is equal to how many KW of single phase .

any body,pls tell me how to done relay coordination ? how to coordinate by TCC curve?how to read the tcc curve?

What is the most accurate way of testing ELCB?ELCB is better than RCD?

which MPU register provides the address from which the next instruction byte is to be fetch?

10Hp, 3-phase, 415v, 50Hz induction motor. The above motor is to run on Star-Delta connection, so how do i make following hardware selection 1) MCB, 2) Contactor, 3) Wire Gage (Depending on P-P current or Line Current), 4) OLR, Please tell in detail how to do the above, so as to get the ans. of it even if the Hp rating changes.

Categories
• Civil Engineering (5075)
• Mechanical Engineering (4444)
• Electrical Engineering (16597)
• Electronics Communications (3915)
• Chemical Engineering (1092)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2987)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1377)