If connecting a temp generator 670KVA .415kv with step up
I am given Generator impedances Z1 Z2 Z0 to 100MVA base. Do
I need to work out the generator fault current by using
these impedances i.e gen rating / impedance. Then use this
as my source impedance for the calculations that follow.
No Answer is Posted For this Question
Be the First to Post Answer
Can any body tell me about Hi-pot test, and why it is necessary and its procedure of testing
what is "PE" earthing? and what do u know abt 16mm cable?
sir , what happen if we decrease ( approx 3 inch ) the lenth of shaft in 110KW Induction , three phase motor. actually a 110KW motor is couppled with star couplling to 120TR compressor. When we doing maintenance in compressor it is required to skid the motor backword and resulting dis- alightnment . so we want to change the tyre coupling in place of existing coupling. so it is required to cut off the rotor aprox 3 inch form driving side.
How to calculate VCB current rating for 2000 KVA transformer
what would happen if reactive power (kvar)is increased (more)or decreased (less)? how much exact reactive power should be maintained? and what should be done for that
Will u plz give me simple diagram for tube light connection & also function of chock?
what are the applications of TIG welding
what is the distance between two overhead lines
i want to know about psu exam eligibility critaria?
HT/LT PANEL TEST?ALL TEST
Testing procedure of DG alternator stability test
sir vizag steel ka junior trainee ka paper kitne number ka ayega