Why secondary of a CT in a power system acts as an open
circuit after core saturation?
Answers were Sorted based on User's Feedback
Answer / arpita
Under normal operating condition m.m.f or ampere- turn
both primary and secondary oppose each other. When
secondary of C.T is open circuited then there is no
demagnetiging ampere-turn to oppose the primary ampere-turn
and therefore, the primary ampere-turns now become active
in producing a very high flux density in the core which
result in very high inductance e.m.f. in the secondary
This high induced e.m.f. is likely to cause
a) Overheating of core
b) Breakdown of insulation
c) An electric shock to the attending personnel.
For these reason secondary of C.T in power system not act
as an open circuit.
|Is This Answer Correct ?||5 Yes||1 No|
Answer / gajanan
there are 2 possibilities
1.if we keep secondary of ct open, then only primary mmf
will be present in core which saturates the core
2.in fault condition due to high frequencu current core
saturates means permeability of core decreases very much as
good as wood
|Is This Answer Correct ?||0 Yes||1 No|
electricity bill multiplication factor 487.20xconsumption=total unit in kwh. what is 487.20 ?
i(1)= j0.5 p.u., i(2)= -j0.5 p.u., i(0) =j1 p.u. What kind of fault it is-- a)l-l ,b)l-l-g, c)l-l-l-g, d)l-g.
why does voltage generation at 11 kv?
What are the differents between Breaker & Contactor?
Dear all,recently in our plant we installed a conveyor for this the motor ratings are 5 hp and Amps 7.39.Due to on urgent starting of conveyor we fix the DOL starter with range of 9-15 amps.give me suggestion regarding on this issue
High voltage test procedure of in swgr board. why should measure millivolt drop on testing time?
A resistance of 50 kΩ has a conductance of:(a) 20S(b) 0.02S(c) 0.02 mS(d) 20 kS
ASTM D 3455 - Standard Test Methods for Compatibility of Construction Material with Electrical Insulating Oil of Petroleum Origin has been used for Testing Transformer Oils with a product placed in it. Aged Control Oil has a Power Factor of 0.032% at 100°C. Aged Oil with a Test component has a Power Factor of 0.093% at 100°. Is this increase acceptable? If not why? How much increase is acceptable?
two parallel conductors are carrying the current in the same direction.which of the following statements is true? (a)there is arepelling force between the conductors (b)the force increases when the distance between the conductors is increased (c)there is an attaracting force between the conductors (d)the force increases when the distance between the conductors is decreased
Apparent power is expressed as V * I(Conjugate). Why not in V * I ?
single phase can run in PVC conduit. Three phase can also run in one PVC conduit. But two phase cannot run in one PVC conduit. WHY? reply plz....awaiting your answer.
Why Dyn11 Transformer is selected for distribution transformer?