Answers were Sorted based on User's Feedback
Answer / visakh ctjv
In ultrasonic level transmitter, a ultrasonic source is
used to produce ultrasonic pulses . these pulses are
transmitted through the vessel,the echo returning back
from the vessel is then recieved by a detector , depending
upon the level in the vessel the frequency of the recieved
signal varries ,the difference between the transmitted
pulse frequency and the recieved signal frequency is used
to measure the level.
|Is This Answer Correct ?||26 Yes||4 No|
Answer / hassanelect
The ideal mounting point for the sensor is directly
underneath the silo roof.
The ultrasonic emitter in the sensor is excited electrically
and sends an ultrasonic pulse in the direction of the
surface of the product. The surface partially reflects the
pulse. This echo is detected by the same sensor, now acting
as a directional microphone, and converted back into an
The time between transmission and reception of the pulse -
the sonic run time - is directly proportional to the
distance between the sensor and the product surface.
The distance D is determined from the velocity of sound c
and the run time t by the formula:
|Is This Answer Correct ?||17 Yes||3 No|
Answer / naabil al-eryani
The transmitter is designed to be mounted above a liquid
and uses ultrasonic pulses to continuously measure the
distance to the liquid surface.
The microprocessor-controlled electronics calculates
distance to the liquid level from the time delay between
the transmitting and receiving of signals.
|Is This Answer Correct ?||7 Yes||0 No|
Explain about safety integrated level protection? . How it was differ from other protections ?
deference between DCS and PLC including date processing and architacture.
what is differance between SOE an alarams
1.what is the power consumption of three element drum level control in sugar industries? 2.how to reduce that?
can any send me a forbes marshall dtron 316 manual
what difeerent between HART and BRAIN?
what is temperature compensation?
how to calibrate any tansmiter by loop or hart calibrator
IN JB CONSTRUCTION WHY WE ARE USING JUMPPER........CAN U PLEASE TELL ME.....
Explain the difference between differial pressure & delta pressure?
How to work temperature gauge?
what are the steps to commissioning a DCS system?