what is the function of NAT & NAC contacts in breaker
control switch (TNC)??
Answers were Sorted based on User's Feedback
Answer / k.prakashchandra
NAT- normal after trip and NAC normal after close.These are
'lost motion contacts' which indicate last operated position
of breaker .With NAC contact we get 'Auto-trip' indication
when the breaker is tripped by relay.
|Is This Answer Correct ?||9 Yes||5 No|
Answer / rajesh t k
The NAT and NAC contacts are provided on TNC switch to facilitate additional functionalities from the TNC switch than mere Tripping or Closing.
These contacts are also known as Lost Motion Contacts. They help identify the last operation (Trip/Close) performed by the operator through the TNC switch.
The NAC contact will be closed whenever the operator turns the TNC lever to Close position and the contacts stays closed even after the lever is returned to the Neutral position by the operator, until the lever is turned to Trip side.
Hence, the 'Auto Trip' indication can be given via the NAC contact(instead of giving through an NO contact of the master trip relay), in series with the CB's 52b contact. That is, this is just an alternate way to wire up the 'Auto Trip' indication.
The NAT contact, likewise will be through whenever the CB has tripped via the TNC lever switch by the operator, until the lever is turned to Close position again.
|Is This Answer Correct ?||1 Yes||0 No|
what is impedance in a transformer? how can i calculate it?
if a 3 phase induction stator has charactristic plate and have on winding inside.with the calculation of plate or dimenssion of core how one can desinge rewinding drawing.
What mean 150 amp hour write on battery.
how to calculate induction motor rating (HP) if name plate is missing from motor at site condition ?
how the fan is switched off immediately switching off the switch?
What is the difference between shortcircuit current, rated current of cable & MCB with example? What will be the size of cable required for 5.5 KW motor (Full load current 10 Amps approx.), Starting current with DOL is 120 Amps. Aprrox. Short circuit current with LLLG fault is 2000 Amps Approx.
How to calculate Battery back up time for a 400 AH Battery bank having a load of 20 Amps and charging time required to fully charge this battery bank?
motor work in hat principle generator work in what principle transformer work in what principle pls explain with details or answered to firstname.lastname@example.org
What is principal to reduce earth leakage current with isolation transformer? When isolation transformer is installed in input stage of system, earth leakage current is reduced. the reason is why the leakage current of 2nd stage of isolation transformer does not affect the 1st stage's leakage current. I would like to know the reason. As you know, earth leakage current is a kind of AC. So, How to reduce earth leakage current in case that isolation transformer is used?
What does the letter CTNM in negative phase sequence relay means?
can you explain the rms value in simple words....
Is it possible to make 0.75KW motor earthing from MCC panel by using the 1.5 SQMM, 4 core cable, means 3 core for 3 Phases & 1 core for Earth terminal?