what is the function of NAT & NAC contacts in breaker
control switch (TNC)??
Answers were Sorted based on User's Feedback
Answer / k.prakashchandra
NAT- normal after trip and NAC normal after close.These are
'lost motion contacts' which indicate last operated position
of breaker .With NAC contact we get 'Auto-trip' indication
when the breaker is tripped by relay.
|Is This Answer Correct ?||9 Yes||5 No|
Answer / rajesh t k
The NAT and NAC contacts are provided on TNC switch to facilitate additional functionalities from the TNC switch than mere Tripping or Closing.
These contacts are also known as Lost Motion Contacts. They help identify the last operation (Trip/Close) performed by the operator through the TNC switch.
The NAC contact will be closed whenever the operator turns the TNC lever to Close position and the contacts stays closed even after the lever is returned to the Neutral position by the operator, until the lever is turned to Trip side.
Hence, the 'Auto Trip' indication can be given via the NAC contact(instead of giving through an NO contact of the master trip relay), in series with the CB's 52b contact. That is, this is just an alternate way to wire up the 'Auto Trip' indication.
The NAT contact, likewise will be through whenever the CB has tripped via the TNC lever switch by the operator, until the lever is turned to Close position again.
|Is This Answer Correct ?||0 Yes||0 No|
What is the result of under frequency to the system.
how was your last weekend.
WHY THE DIMENSION OF TWO SAME RATED MACHINE IS DIFFERENT ?
what is the mechanical safety of DG ?
what causes contact chatter when there is no demand on the air conditioning unit?
wil a dc motor run without a starter??
Consider a case that two 200 hp motors are connected to 500KVA transformer. For improving power factor can we add capacitors in common bus bars to motors. Or should we add capacitors for each individual motor?
Phase control and integral control are used for?
what is the difference between electrical choke and electronic choke?
what is meant by re-rolling motor? how it differs from standard motor?
what happend if we remove dc exciter from moving machine..: gg
what is basic difference between the normal tube light choke and electionic choke ?