formula for cable size calculation for current?
Answers were Sorted based on User's Feedback
Answer / govardhana rao.p
Calculations are same as above but for 50A load
We can use the bellow cables
Aluminium: 50 x 3.5 Core
Cu : 16 x 4 Core
|Is This Answer Correct ?||115 Yes||61 No|
Answer / sabu
in case 50amps 230v single phase load we can use 16mm aluminium and 10mm copper
|Is This Answer Correct ?||29 Yes||6 No|
Answer / zafar
the answer is not correct the correct figure is 25mmsq
|Is This Answer Correct ?||37 Yes||19 No|
Answer / bipin naik
The current will be 27 A for single phase supply(230v)
|Is This Answer Correct ?||4 Yes||0 No|
Answer / fathi
2x10 sqmm Cu/XLPE/PVC 600/1000 v
|Is This Answer Correct ?||17 Yes||16 No|
Answer / engr.muhammad younas khan
SINGLE PHASE FORMULA FOR CABLE SIZING.
I :- AMPERES
L :- LENGTH OF CABLE.
K :- CONDUCTIVITY OF COPPER(58)
:- CONDUCTIVITY OF ALUMINUM (36)
Vd:- VOLTAGE DROP.
I:- 50 AMPERES.
L:- 100 METERS.
Vd:- 3% ACCEPTABLE OF 230 VOLTS
AREA (mm2)= 2*I*L/(K*Vd)
= 24.98 mm2
= ALMOST 25 mm2
FOR THREE PHASE:
AREA(mm2) = 1.732*50*100/(58*12)
= 12.44 mm2
= ALMOST 15 mm2
3% voltage drop of 400 volts =12 volts.
ABOVE EXPLAINED FOR IS PROPERLT CORRECT.USE AND ENJOY.
ENGR.MUHAMMAD YOUNAS KHAN
WAZIRABAD CITY,PUNJAB, PAKISTAN
|Is This Answer Correct ?||2 Yes||2 No|
Answer / selvakumar
230 meter cable
|Is This Answer Correct ?||2 Yes||3 No|
Answer / lorp soophan
|Is This Answer Correct ?||0 Yes||4 No|
Answer / vinay katoch
formula is same but for 50 amp load we can use 3.5c
25mmseq.all.and 10mm seq.cu.
|Is This Answer Correct ?||18 Yes||28 No|
Answer / gurunadharaov
by the formula p=v*i*cos@
assume the load as 5kw and operating at 230v and also
assume the load as inductive (so the power factor is 0.5
now by formula
NOW CABLE SIZE MUST BE > LOAD
SO CABLE SIZE IZ 65SQMM(ITZ DSSEPEND ON AL/CU CABLE)
|Is This Answer Correct ?||118 Yes||136 No|
How can two 3 phase transformers of same KVA and Voltage be connected in parallel?
why neutral and body earthing of transformers kept separated? what is distance between two is required as per is?
what ispositive, negative, zero sequence impedence?
Do any one know exacatly when the results for NHPC held on 8th march 09 for engineering trainees will be released ?. if so please post it, i'm eager to know it.
two generator runnig with parallel but only one NGR on And one off Why
how many types of transformer.
What does a Bode plot tell you?
How can claculate to attain the desired PF in the line ( HOW Much KVAR is required ) Pls Give the formula? Equate Petrochemical 0 1 how to calculate sizing of NGTR (Transformer rating,Loading resistor value and Current rating of resistor) and what is the X/R ratio. Details : 11kV,Capacitance 1.73532 micro farads,40kA for 1sec. 0 1 What will happened. if we feed 3phase supplay to the stater with out insert the rotor. How much current will flow through the stater winnding? Equate Petrochemical 0 1 What is required of exietation to the alternater. 0 1 why star point of HT motor not earthed? Equate Petrochemical 0 1 Why we are getting low voltage in star connection? Equate Petrochemical 0 2 What's ND relay & it's functions? Equate Petrochemical 0 2 How instantanious short circuit current is calculated? its formula? Equate Petrochemical 0 2 What is servo Motor? What's the advantages of this motor over Induction motor? Equate Petrochemical 0 2 What is core CT & it's function? Equate Petrochemical 0 3 what is meant by star/delta voltages as 440/220 in a 3 phase induction motor, and why it should be connected on STAR IN 3 PHASE SUPPLY L & T 0 4 What is required of exietation to the alternater. KNB 1 23 what is the design voltage for 6.6KV 2000 KVAR HT capacitor? Consultancy 0 3 Pls explain about vfd control?Where it is used, Give some example? siemens 1 22 Please explain me abt PQ diagaram in the power sector. 0 9
why to use 50hz only in tansmisson and as well as in distribution why not60hz?
what is the reasons for blowing fuse
How power factor of electric system improved?
What is the unit of attenuation?