Answer / avinit saha
A busbar is a copper plate/bar which is used in main and emergency switchboards to conduct electricity from generators or from one electrical terminal to another. Busbar Inspection and maintenance is carried out by
1.Carryout visual inspection of copper plate and nut bolts. Mark any missing or burn out areas.
2.By hand or using a metal or plastic stick (where access for hand is not possible), tap the bus plates gently so as to make out for any loose connection. Ensure to wear electrical gloves even when bus bar is not live.
3.The busbars are mechanical supported inside the switchboard by means of insulators, which may be of rubber or ceramic materials (bad conductors). Check for any damages in the insulator part.
4.By using an adjustable spanner or particular size spanner, tighten the nuts in the busbar connection for main and emergency switch boards.
5.Check the tightness of the wire connections, which is connected to the circuit breakers.
6.Clean the bus bar and switchboard area with the help of vacuum cleaner.
7.If u find any loose connection or spark, black-out the particular and adjacent bus bar before tightening the nut.
8.If u find any metal piece or nut bolts missing or inside the panel, ensure to remove it as the same can cause short circuit or fire
|Is This Answer Correct ?||1 Yes||0 No|
what is Fault level? why it is calculated? how will u decide same for our plant?
which relay is used on long transmission lines
why are caluculte transformers or dg's in kva does not caluculate in kw
Why donot sleep below the tree for night time?
sir please send me previous year questions of jspl through which i could prepare myself fpr the test.
What is the full form of AND,OR and other logic gates
what is purpose of using neutral grounding transformer in generators??
we use 3 phase supply for induction motor why not use two phase supply .
What is the difference between class0.1 and class 0.1s accuracy of current transformers
what is power load and lighiting load?
what condition there autotransformer will fail?
1- What is the Polarization Index number be good for 15KV 3c#500MCM electrical cable? 2- Can I use the IEEE Std 43-2000 to perfom the PI test? Thanks