why we grounding the neutral of a transformer?
Answers were Sorted based on User's Feedback
Answer / alok das
To grounding the neutral of a transformer becease this time
neutral is works as earthing. And the earthing safety they
transformer by any kinds of electrical falts. over load
current & lighting.
|Is This Answer Correct ?||5 Yes||0 No|
Answer / bhavesh patel
grounding of neutral is because of whenever there is fault in equipment, the excessive current flow through in it and it will ground through neutral wire
|Is This Answer Correct ?||1 Yes||1 No|
Answer / simon peter
In distribution transformer the secondary side is always in star connection i,.e a neutal piont is drawn. Neutal wire & the core of x-mer is connected to earthing bcs if there is enormous load variation the overall load will b on phase wires hense x-mer might blow off due to increase in the value of hysteresis & eddy losses........
|Is This Answer Correct ?||2 Yes||2 No|
HOW CIRCUIT BREAKER RATING CALCULATED?WHAT ARE THE PARAMETERS CONSIDERED?
What is the difference between XLPE & FRLS cables? Is FRLS cables is a type of XLPE cable or both r different?
Is a DC Transformer Possible? if Yes, Then Why, if not Then Why?
any idea abt REVERSE METERING concept.........?
I have 2 transformers in two different plants, both are without OLTC but i am facing problem of voltage fluctuation at LV side from only one transformer. i have to change its taps manually twice in a day. Another transformer delivering voltage is ok. Please guide me about the problem
Material commonly used in making transformer core is A cast iron B mild steel C high silicom steel D high carbon steel
Current Capacity of 55sqmm & 80sqmm conductor
what is meant by substation?
why asa method ZPF method is more accurate than ASA method?
in slip ring motor if motor specification is given how we calculate its rotor resistance in starting
what is the advantages of having in-built acvvvf (without seperate inverter in the control panel)in the drive system of elevators?
What is the minimum setting in REF relay because i am facing some problem whenever power resumes after power failure my transformer is tripping because of REF trip. I am using CSPC make numerical relay(DIP switches). Now setting is 15 percentage. What is the reason for this triping. I sm waiting for answer